Standards as High as Your Own
NECA Online Help Desk Please leave a message
I have adjoining restaurants with separate meters, disconnects and service locations. They want to use power from one tenant for a led tape light in a window blocked by a 1hr shared fire wall in the other tenants' space. I know 400.7, 400.8 for the cord reasons Can they really share power by code? You would have to disconnect 2 different locations.
Hey Ben thanks for your question. It is not clear what you mean by a window that is blocked by a shared fire wall. And why would "they" want to use power from one tenant space to supply equipment in another space, but here are some thoughts.
Branch circuits used for common areas of multi-occupancy buildings cannot be supplied from one of the tenant spaces as stated in 210.25. That does not seem to be the case in your situation if the "LED tape light" is in the other tenant's space - it is not in a common area. Each occupant must have ready access to overcurrent devices for conductors supplying that occupancy as stated in 240.24(B). That might prohibit what is being proposed depending on how "ready access" is defined or determined. Check with the AHJ to get their position.
ABOUT CQD: NECA’s Code Question of the Day (CQD) is a leading National Electrical Code® forum for NECA and the industry. The CQD generates a lively dialogue and relative practical and Code-based responses to an ever-increasing and interactive audience.
IMPORTANT NOTICE: All answers are based on the latest edition of the National Electrical Code®, unless the question requests a response based on a specific edition. This correspondence is not a formal interpretation of the NEC®. Any responses expressed to the questions are opinions and do not necessarily represent the official position of NECA, NFPA, or any technical committee. In addition, this correspondence is neither intended, nor should it be relied upon, to provide professional consultation or services.
ABOUT CHARLIE: Charles M. Trout, better known as Charlie, was a nationally known NEC® expert and author. He served on several NEC® technical committees and is past chairman of CMP-12. In 2006 Charlie was awarded the prestigious Coggeshall Award for outstanding contributions to the electrical contracting industry, codes and standards development, and technical training. Charlie was also a member of NECA’s Academy of Electrical Contracting. Charlie’s experienced team of industry experts keep the CQD dialogue and discussions active and informative in the spirit of the man himself, as he wanted.
NECA STANDARDS: NECA publishes the National Electrical Installation Standards™ (NEIS™), a series of ANSI-approved performance and quality standards for electrical construction. Visit NECA-NEIS.org for more information. NEISÃ” can be purchased in three formats: as paper books, on CD, or as electronic downloads.
NECA SAFETY PRODUCTS: NECA publishes valuable electrical safety books and CDs for the industry. Visit necanet.org/store to view or purchase NECA safety products.
CONTACT US: To submit a Code question, subscribe, or unsubscribe from this list, please e-mail: email@example.com.
© 1999 – 2014 National Electrical Installation Standards. All rights reserved.
Brought to you by NECA. NECA is the voice of the electrical contracting industry NATIONAL ELECTRICAL INSTALLATION STANDARDS, NEIS and the NEIS logo are registered trademarks of the National Electrical Contractors Association.
Created by Matrix Group International, Inc.