Standards as High as Your Own
NECA Online Help Desk Please leave a message
Love the service you provide.
While it’s clear in 250.64 that a grounding electrode conductor metal conduit requires bonding at both ends, does this rule apply to IT equipment bonding with a bonding conductor sleeved in a metal conduit?
Hey Ed thanks for your question and the compliment. You are correct grounding electrode conductors installed in ferrous metal raceways and enclosures must be bonded at each end as stated in 250.64(E). This is to minimize the choke effect of ferrous enclosures. Communication systems have specific rules in 770.100(A)(6), 800. 100(A)(6), 810.21(D), 820. 100(A)(6), and 830. 100(A)(6), that also require bonding conductors and grounding electrode conductors in metal raceways to be bonded at both ends. You don't mention what the Information Technology Equipment is for but Article 645 does not have the same requirement. Possibly it should, if it performing the same function, and you can submit a Public Input to add that rule for the 2023 NEC.
ABOUT CQD: NECA’s Code Question of the Day (CQD) is a leading National Electrical Code® forum for NECA and the industry. The CQD generates a lively dialogue and relative practical and Code-based responses to an ever-increasing and interactive audience.
IMPORTANT NOTICE: All answers are based on the latest edition of the National Electrical Code®, unless the question requests a response based on a specific edition. This correspondence is not a formal interpretation of the NEC®. Any responses expressed to the questions are opinions and do not necessarily represent the official position of NECA, NFPA, or any technical committee. In addition, this correspondence is neither intended, nor should it be relied upon, to provide professional consultation or services.
ABOUT CHARLIE: Charles M. Trout, better known as Charlie, was a nationally known NEC® expert and author. He served on several NEC® technical committees and is past chairman of CMP-12. In 2006 Charlie was awarded the prestigious Coggeshall Award for outstanding contributions to the electrical contracting industry, codes and standards development, and technical training. Charlie was also a member of NECA’s Academy of Electrical Contracting. Charlie’s experienced team of industry experts keep the CQD dialogue and discussions active and informative in the spirit of the man himself, as he wanted.
NECA STANDARDS: NECA publishes the National Electrical Installation Standards™ (NEIS™), a series of ANSI-approved performance and quality standards for electrical construction. Visit NECA-NEIS.org for more information. NEISÃ” can be purchased in three formats: as paper books, on CD, or as electronic downloads.
NECA SAFETY PRODUCTS: NECA publishes valuable electrical safety books and CDs for the industry. Visit necanet.org/store to view or purchase NECA safety products.
CONTACT US: To submit a Code question, subscribe, or unsubscribe from this list, please e-mail: email@example.com.
© 1999 – 2014 National Electrical Installation Standards. All rights reserved.
Brought to you by NECA. NECA is the voice of the electrical contracting industry NATIONAL ELECTRICAL INSTALLATION STANDARDS, NEIS and the NEIS logo are registered trademarks of the National Electrical Contractors Association.
Created by Matrix Group International, Inc.