Standards as High as Your Own
NECA Online Help Desk Please leave a message
Re: CQD answer published February 22 and March 4, 2019 -Flexible Cords
I had really hoped there would be many more comments and info regarding the difference between cable and cord. My personal overly-simplified impression and rule-of-thumb these days is that:
CABLE can be used to connect between components of a system (i.e. robotic arm sections, power supply to powered device, etc) but that only CORD (limited to the insulation types defined in Table 400.4) can touch the floor, and/or connect to bldg power (whether with a plug or hard-wired.)
Hey Perry thanks for your comments. Cable, raceway and other wiring methods must be secured and supported based on the specific XXX.30 section of the applicable article. But they are not prohibited from being on or contacting floors, they can actually be secured to and supported by floors.
Flexible cords can be used if necessary, for flexibility - such as portions of robots based on 400.10(9). Some judgment is necessary when determining what is acceptable based on the conditions.
As we previously said, from a simplistic view, cables are in Chapter 3 and flexible cords are in Article 400.
ABOUT CQD: The Code Question of the Day (CQD) is NECA and ELECTRICAL CONTRACTOR Magazine’s flagship National Electrical Code (NEC®) public forum for the industry, sponsored by EATON. The daily distribution of Q&A generates a lively dialogue and shares relative Code-based practical responses.
SUBMIT YOUR CODE QUESTION: Click here to submit a question to for inclusion in an upcoming edition of the Code Question of the Day, or email email@example.com.
CHARLIE TROUT: Charles M. Trout, better known as Charlie, was a nationally recognized NEC® expert and author. He served on several NEC technical committees and is past chairman of CMP-12. In 2006, Charlie was awarded NECA’s prestigious Coggeshall Award for outstanding contributions to the electrical contracting industry, codes and standards development and technical training. NECA continues to provide this public forum in memory and recognition of all his fine contributions that has made the NEC what it is today.
NECA STANDARDS: NECA publishes the National Electrical Installation Standards™ (NEIS™), a series of ANSI-approved performance and quality standards for electrical construction. NEIS can be purchased in the NECA Store in three formats: a printed or PDF download of a standard or, as an annual subscription service.
NECA SAFETY PRODUCTS & PUBLICATIONS: NECA produces electrical safety publications and products for the industry including jobsite safety guides, handbooks and resource kits. View a full listing of available resources and products »
IMPORTANT NOTICE: Unless the question requests a response based on a specific edition, all answers are based on the latest edition of NFPA 70® National Electrical Code®.
This correspondence is not a formal interpretation of the NEC® and any responses expressed to the questions are opinions and do not necessarily represent the official position of NECA, NFPA, the NEC Correlating Committee any Code-making panel or other electrical technical committee. In addition, this correspondence is neither intended, nor should it be relied upon, to provide professional consultation or services.
UPDATE YOUR SUBSCRIPTION PREFERENCES: Subscribe or Unsubscribe from this list.
© 1999 – 2014 National Electrical Installation Standards. All rights reserved.
Brought to you by NECA. NECA is the voice of the electrical contracting industry NATIONAL ELECTRICAL INSTALLATION STANDARDS, NEIS and the NEIS logo are registered trademarks of the National Electrical Contractors Association.
Created by Matrix Group International, Inc.