Standards as High as Your Own
NECA Online Help Desk Please leave a message
Good day, Has anyone else noticed the requirement to disconnect the grounded conductor from a fuel dispenser has disappeared? The 2017 NEC apparently lost this requirement that has been around for many years. Any insight as to why? I understand this was an effort to match NFPA 30A 6.7 but is it no longer necessary to disconnect the grounded conductor?
Hey Grant thanks for your question. You are correct 514.11 was revised in the 2017 NEC based on First Revision No. 3996. There were two Public Inputs that addressed the location of emergency shutoff devices or electrical disconnects for both attended and unattended self-service motor fuel dispensing facilities. The panel statement in the First Draft Report for FR3996 is " Section 514.11 is revised to reflect the requirements in NFPA 30A- 2015." No other explanation for the removal of the specific rule for disconnecting grounded conductors. If anyone, such as from CMP14, knows of the specific reason please send in a comment and we will publish it.
ABOUT CQD: NECA’s Code Question of the Day (CQD) is a leading National Electrical Code® forum for NECA and the industry. The CQD generates a lively dialogue and relative practical and Code-based responses to an ever-increasing and interactive audience.
IMPORTANT NOTICE: All answers are based on the latest edition of the National Electrical Code®, unless the question requests a response based on a specific edition. This correspondence is not a formal interpretation of the NEC®. Any responses expressed to the questions are opinions and do not necessarily represent the official position of NECA, NFPA, or any technical committee. In addition, this correspondence is neither intended, nor should it be relied upon, to provide professional consultation or services.
ABOUT CHARLIE: Charles M. Trout, better known as Charlie, was a nationally known NEC® expert and author. He served on several NEC® technical committees and is past chairman of CMP-12. In 2006 Charlie was awarded the prestigious Coggeshall Award for outstanding contributions to the electrical contracting industry, codes and standards development, and technical training. Charlie was also a member of NECA’s Academy of Electrical Contracting. Charlie’s experienced team of industry experts keep the CQD dialogue and discussions active and informative in the spirit of the man himself, as he wanted.
NECA STANDARDS: NECA publishes the National Electrical Installation Standards™ (NEIS™), a series of ANSI-approved performance and quality standards for electrical construction. Visit NECA-NEIS.org for more information. NEISÃ” can be purchased in three formats: as paper books, on CD, or as electronic downloads.
NECA SAFETY PRODUCTS: NECA publishes valuable electrical safety books and CDs for the industry. Visit necanet.org/store to view or purchase NECA safety products.
CONTACT US: To submit a Code question, subscribe, or unsubscribe from this list, please e-mail: firstname.lastname@example.org.
© 1999 – 2014 National Electrical Installation Standards. All rights reserved.
Brought to you by NECA. NECA is the voice of the electrical contracting industry NATIONAL ELECTRICAL INSTALLATION STANDARDS, NEIS and the NEIS logo are registered trademarks of the National Electrical Contractors Association.
Created by Matrix Group International, Inc.