Standards as High as Your Own
NECA Online Help Desk Please leave a message
2017 NEC code question: So I’m installing low voltage 12vac luminaire to a deck post near a pool/spa/inground hot tub. It is located little over 5 feet away from the inside wall and up 8 feet heigh. Art. 411.5 (b) says no less than 10 feet from nearest edge of pool unless permitted by article 680. So when I go to 680.22 (b)(6) it talks about within 5 feet with low voltage Luminaires. But my measurements are outside of 5 feet and 8 feet high . So when I look at 680.22 (b) 4 it looks like it just has to be rigidly attached because I’m over 5 feet heigh? I just don’t know if that means low voltage luminaries also ? What part of 680.22 does my installation fall under? Thanks Steve
Hey Steve thanks for your question. The wording is not extremely clear but your installation is covered by 680.22(B)(6). Luminaires, lighting outlets and ceiling-suspended (paddle) fans, such as those on 120-volt circuits, between 5 and 10 feet horizontally from the inside walls, must have GFCI protection - unless they are at least 5 feet above the maximum water level and rigidly attached as stated in 680.22(B)(4). Listed low voltage luminaires that do not require grounding, and that don't exceed the low-voltage contact limit (as defined in 680.2) and are supplied by listed power supplies that are identified for swimming pool and spa use [680.23(A)(2)] are allowed within 5 from the inside walls of the pool as stated in 680.22(B)(6). If they are allowed inside the 5 ft dimension it makes sense, they would also be allowed beyond that dimension but that wording is missing. Make sure you also follow the instructions for the equipment.
ABOUT CQD: NECA’s Code Question of the Day (CQD) is a leading National Electrical Code® forum for NECA and the industry. The CQD generates a lively dialogue and relative practical and Code-based responses to an ever-increasing and interactive audience.
IMPORTANT NOTICE: All answers are based on the latest edition of the National Electrical Code®, unless the question requests a response based on a specific edition. This correspondence is not a formal interpretation of the NEC®. Any responses expressed to the questions are opinions and do not necessarily represent the official position of NECA, NFPA, or any technical committee. In addition, this correspondence is neither intended, nor should it be relied upon, to provide professional consultation or services.
ABOUT CHARLIE: Charles M. Trout, better known as Charlie, was a nationally known NEC® expert and author. He served on several NEC® technical committees and is past chairman of CMP-12. In 2006 Charlie was awarded the prestigious Coggeshall Award for outstanding contributions to the electrical contracting industry, codes and standards development, and technical training. Charlie was also a member of NECA’s Academy of Electrical Contracting. Charlie’s experienced team of industry experts keep the CQD dialogue and discussions active and informative in the spirit of the man himself, as he wanted.
NECA STANDARDS: NECA publishes the National Electrical Installation Standards™ (NEIS™), a series of ANSI-approved performance and quality standards for electrical construction. Visit NECA-NEIS.org for more information. NEISÃ” can be purchased in three formats: as paper books, on CD, or as electronic downloads.
NECA SAFETY PRODUCTS: NECA publishes valuable electrical safety books and CDs for the industry. Visit necanet.org/store to view or purchase NECA safety products.
CONTACT US: To submit a Code question, subscribe, or unsubscribe from this list, please e-mail: firstname.lastname@example.org.
© 1999 – 2014 National Electrical Installation Standards. All rights reserved.
Brought to you by NECA. NECA is the voice of the electrical contracting industry NATIONAL ELECTRICAL INSTALLATION STANDARDS, NEIS and the NEIS logo are registered trademarks of the National Electrical Contractors Association.
Created by Matrix Group International, Inc.