Standards as High as Your Own
NECA Online Help Desk Please leave a message
Re: CQD answer published Thursday, January 10, 2018 - Continuous Loads
I'd like to just comment on the CB or OCPD rating of the feeder. The ampacity is determined by the method described, 125% of the anticipated full load. The OCPD then can be selected base on that. For feeders, the standard size value for OCPD can be rounded down from that ampacity rating, not up as required for branch circuits.
Best regards, Nick Abbatiello
Hey Nick thanks for you comment. You are correct the feeder must be sized to have an ampacity at least (minimum) 125% of the load, if it is a continuous load, as stated in 215.2(A)(1)(a). The overcurrent device must also be sized to at least 125% of a continuous load as stated in 215.3. You might be able to round down from the conductor ampacity but it cannot be rated less than 125% of the load, whether or not it is a standard size. These rules are the same for branch circuits in 210.19 and 210.20.
ABOUT CQD: NECA’s Code Question of the Day (CQD) is a leading National Electrical Code® forum for NECA and the industry. The CQD generates a lively dialogue and relative practical and Code-based responses to an ever-increasing and interactive audience.
IMPORTANT NOTICE: All answers are based on the latest edition of the National Electrical Code®, unless the question requests a response based on a specific edition. This correspondence is not a formal interpretation of the NEC®. Any responses expressed to the questions are opinions and do not necessarily represent the official position of NECA, NFPA, or any technical committee. In addition, this correspondence is neither intended, nor should it be relied upon, to provide professional consultation or services.
ABOUT CHARLIE: Charles M. Trout, better known as Charlie, was a nationally known NEC® expert and author. He served on several NEC® technical committees and is past chairman of CMP-12. In 2006 Charlie was awarded the prestigious Coggeshall Award for outstanding contributions to the electrical contracting industry, codes and standards development, and technical training. Charlie was also a member of NECA’s Academy of Electrical Contracting. Charlie’s experienced team of industry experts keep the CQD dialogue and discussions active and informative in the spirit of the man himself, as he wanted.
NECA STANDARDS: NECA publishes the National Electrical Installation Standards™ (NEIS™), a series of ANSI-approved performance and quality standards for electrical construction. Visit NECA-NEIS.org for more information. NEISÃ” can be purchased in three formats: as paper books, on CD, or as electronic downloads.
NECA SAFETY PRODUCTS: NECA publishes valuable electrical safety books and CDs for the industry. Visit necanet.org/store to view or purchase NECA safety products.
CONTACT US: To submit a Code question, subscribe, or unsubscribe from this list, please e-mail: email@example.com.
© 1999 – 2014 National Electrical Installation Standards. All rights reserved.
Brought to you by NECA. NECA is the voice of the electrical contracting industry NATIONAL ELECTRICAL INSTALLATION STANDARDS, NEIS and the NEIS logo are registered trademarks of the National Electrical Contractors Association.
Created by Matrix Group International, Inc.