Standards as High as Your Own
NECA Online Help Desk Please leave a message
I'm in Tennessee. I have a newly finished 3br/2ba house. 200A service. I have a small garage that I'm trying to bring power to. I have four spare breaker spaces. I was planning on adding a 150A sub panel in a detached garage using direct burial cable and spare breaker spaces in the house panel. My question is, will I need to mount a meter-base on the exterior of the garage and bring new service instead of just OCP'ing the 150A with a breaker inside the house panel, a disconnect outside the garage, and another 150A main breaker inside the subpanel? Some local guys told me that since the garage isn't ATTACHED it has to have it's own meter, which kind of defeats the purpose of using the spare breaker spaces. I'm trying to keep from doing this work twice
Hey Zach thanks for your question. Buildings and structures can be supplied by services or feeders or branch circuits by using Article 230 or Article 225 - unless there are local requirements that change that. The NEC does not require meters, those are required by utilities because they want to charge for the electric supply and usage. If the house service panelboard is suitable for the additional load of the detached garage using a feeder to supply the garage is acceptable. make sure you locate the garage panelboard to comply with 225.32. That is a very common practice.
ABOUT CQD: NECA’s Code Question of the Day (CQD) is a leading National Electrical Code® forum for NECA and the industry. The CQD generates a lively dialogue and relative practical and Code-based responses to an ever-increasing and interactive audience.
IMPORTANT NOTICE: All answers are based on the latest edition of the National Electrical Code®, unless the question requests a response based on a specific edition. This correspondence is not a formal interpretation of the NEC®. Any responses expressed to the questions are opinions and do not necessarily represent the official position of NECA, NFPA, or any technical committee. In addition, this correspondence is neither intended, nor should it be relied upon, to provide professional consultation or services.
ABOUT CHARLIE: Charles M. Trout, better known as Charlie, was a nationally known NEC® expert and author. He served on several NEC® technical committees and is past chairman of CMP-12. In 2006 Charlie was awarded the prestigious Coggeshall Award for outstanding contributions to the electrical contracting industry, codes and standards development, and technical training. Charlie was also a member of NECA’s Academy of Electrical Contracting. Charlie’s experienced team of industry experts keep the CQD dialogue and discussions active and informative in the spirit of the man himself, as he wanted.
NECA STANDARDS: NECA publishes the National Electrical Installation Standards™ (NEIS™), a series of ANSI-approved performance and quality standards for electrical construction. Visit NECA-NEIS.org for more information. NEISÃ” can be purchased in three formats: as paper books, on CD, or as electronic downloads.
NECA SAFETY PRODUCTS: NECA publishes valuable electrical safety books and CDs for the industry. Visit necanet.org/store to view or purchase NECA safety products.
CONTACT US: To submit a Code question, subscribe, or unsubscribe from this list, please e-mail: email@example.com.
© 1999 – 2014 National Electrical Installation Standards. All rights reserved.
Brought to you by NECA. NECA is the voice of the electrical contracting industry NATIONAL ELECTRICAL INSTALLATION STANDARDS, NEIS and the NEIS logo are registered trademarks of the National Electrical Contractors Association.
Created by Matrix Group International, Inc.