Standards as High as Your Own
NECA Online Help Desk Please leave a message
I'm currently a student in the F.E.A.T. school in Florida and I notice there are a ton of mentions to "subject to physical damage" or "severe physical damage". I have asked my teachers and my boss if it's defined anywhere what physical damage covers. The only answer I've gotten that makes sense is thru my boss stating that the determination of what physical damage is, is left to the AHJ that runs the area. My question is just if there is a detention anywhere for what all is subject to physical damage or is it like my boss stated it is just up to the AHJ? I was curious is there was another book that might state it or not. Thank you for your time and hopefully hear from you soon
Hey Devon thanks for your question and congratulations on getting an education to become an electrician. There are several rules about physical damage protection in 300.4 and the wiring methods themselves have additional rules. As example, Electrical Metallic Tubing is not allowed where subject to severe physical damage as stated in 358.12(1) but there is no similar restriction for Rigid Metal conduit in Article 344. If damage to the contained conductors is likely, that is often considered a situation that is exposed to severe physical damage, such as areas with vehicle traffic. Neither term is defined in the NEC so your boss is essentially correct, other than the part about "running the area", the final approval decision is up to the AHJ as stated in 110.2.
ABOUT CQD: NECA’s Code Question of the Day (CQD) is a leading National Electrical Code® forum for NECA and the industry. The CQD generates a lively dialogue and relative practical and Code-based responses to an ever-increasing and interactive audience.
IMPORTANT NOTICE: All answers are based on the latest edition of the National Electrical Code®, unless the question requests a response based on a specific edition. This correspondence is not a formal interpretation of the NEC®. Any responses expressed to the questions are opinions and do not necessarily represent the official position of NECA, NFPA, or any technical committee. In addition, this correspondence is neither intended, nor should it be relied upon, to provide professional consultation or services.
ABOUT CHARLIE: Charles M. Trout, better known as Charlie, was a nationally known NEC® expert and author. He served on several NEC® technical committees and is past chairman of CMP-12. In 2006 Charlie was awarded the prestigious Coggeshall Award for outstanding contributions to the electrical contracting industry, codes and standards development, and technical training. Charlie was also a member of NECA’s Academy of Electrical Contracting. Charlie’s experienced team of industry experts keep the CQD dialogue and discussions active and informative in the spirit of the man himself, as he wanted.
NECA STANDARDS: NECA publishes the National Electrical Installation Standards™ (NEIS™), a series of ANSI-approved performance and quality standards for electrical construction. Visit NECA-NEIS.org for more information. NEISÃ” can be purchased in three formats: as paper books, on CD, or as electronic downloads.
NECA SAFETY PRODUCTS: NECA publishes valuable electrical safety books and CDs for the industry. Visit necanet.org/store to view or purchase NECA safety products.
CONTACT US: To submit a Code question, subscribe, or unsubscribe from this list, please e-mail: email@example.com.
© 1999 – 2014 National Electrical Installation Standards. All rights reserved.
Brought to you by NECA. NECA is the voice of the electrical contracting industry NATIONAL ELECTRICAL INSTALLATION STANDARDS, NEIS and the NEIS logo are registered trademarks of the National Electrical Contractors Association.
Created by Matrix Group International, Inc.