Standards as High as Your Own
NECA Online Help Desk Please leave a message
Re: CQD answer published Thursday, February 21, 2019 -
Re Wed Feb 20 CQD about phase conductors separated into different conduits. Your answer is perfect - and I am only accenting the excellent but easily missed concept of 300.20(B). We did this for a 3-foot long, 1600 amp, 3-Phase run between a buss-duct terminal and the machine's input box. Matching lengths of these very short conductors would have been very difficult had we not run them as lug-aligned A - B - C conduits. We used non-metallic (PVC) conduits as is necessary, BUT you must also remember to comply with 300.20(B) by cutting slots between the conduit holes if the enclosure is metallic . Otherwise that sheet of metal becomes an induction heater. Of course, full circuit-sized EGC conductors are required in each conduit.
Hey Scott thanks for your comments and confirming our answer. The example you shared is a good one where installing the "phase conductors" in separate raceways could be necessary to facilitate making the terminations. Cutting slots between the raceway entries in metal enclosures is a common method of preventing heating caused by induced currents.
ABOUT CQD: NECA’s Code Question of the Day (CQD) is a leading National Electrical Code® forum for NECA and the industry. The CQD generates a lively dialogue and relative practical and Code-based responses to an ever-increasing and interactive audience.
IMPORTANT NOTICE: All answers are based on the latest edition of the National Electrical Code®, unless the question requests a response based on a specific edition. This correspondence is not a formal interpretation of the NEC®. Any responses expressed to the questions are opinions and do not necessarily represent the official position of NECA, NFPA, or any technical committee. In addition, this correspondence is neither intended, nor should it be relied upon, to provide professional consultation or services.
ABOUT CHARLIE: Charles M. Trout, better known as Charlie, was a nationally known NEC® expert and author. He served on several NEC® technical committees and is past chairman of CMP-12. In 2006 Charlie was awarded the prestigious Coggeshall Award for outstanding contributions to the electrical contracting industry, codes and standards development, and technical training. Charlie was also a member of NECA’s Academy of Electrical Contracting. Charlie’s experienced team of industry experts keep the CQD dialogue and discussions active and informative in the spirit of the man himself, as he wanted.
NECA STANDARDS: NECA publishes the National Electrical Installation Standards™ (NEIS™), a series of ANSI-approved performance and quality standards for electrical construction. Visit NECA-NEIS.org for more information. NEISÃ” can be purchased in three formats: as paper books, on CD, or as electronic downloads.
NECA SAFETY PRODUCTS: NECA publishes valuable electrical safety books and CDs for the industry. Visit necanet.org/store to view or purchase NECA safety products.
CONTACT US: To submit a Code question, subscribe, or unsubscribe from this list, please e-mail: email@example.com.
© 1999 – 2014 National Electrical Installation Standards. All rights reserved.
Brought to you by NECA. NECA is the voice of the electrical contracting industry NATIONAL ELECTRICAL INSTALLATION STANDARDS, NEIS and the NEIS logo are registered trademarks of the National Electrical Contractors Association.
Created by Matrix Group International, Inc.