Standards as High as Your Own
NECA Online Help Desk Please leave a message
Re: CQD answer published December 20 and 8, 2017 - Physical Damage Protection 1
I don't understand Exhibit 300.1 in the 2017 handbook. Why these types of plates are approved and listed when they do not cover the sides of the stud an 1 1/4" both ways. I know the picture is pertaining to the thickness of the metal. But why show a picture that is in my mind a clear code violation. And why are these plates listed and approved like this. Or am I wrong in assuming the side of the 2 by 4 studs needs to be protected?
Hey Steve thanks for your follow up question you make an interesting point. The wording is different regarding bored holes compared to installations that are parallel to framing members. Cables installed parallel to framing members and furring strips must be at least 1 1/4 inches from the nearest edge of the framing member or furring strip, where nails or screws are likely to penetrate as stated in 300.4(D). The edge of holes in "framing members" must be at least 1 1/4 inches from the nearest edge as stated in 300.4(A)(1). If the 1 1/4 distance is not maintained a steel plate of other means of physical protection that is at least 1/16 inch thick and of appropriate length and width to cover the wiring area, must be provided. Exception 2 in both subdivisions allows a plate to be less than 1/16 inch thick if it is listed and marked as providing equal or better protection. For cables installed through framing members there is no wording that specifies a distance beyond the framing member (side) where physical protection is necessary. Exhibit 300.1 in the 2017 NFPA NEC Handbook is an example of a commonly accepted method of protection.
ABOUT CQD: NECA’s Code Question of the Day (CQD) is a leading National Electrical Code® forum for NECA and the industry. The CQD generates a lively dialogue and relative practical and Code-based responses to an ever-increasing and interactive audience.
IMPORTANT NOTICE: All answers are based on the latest edition of the National Electrical Code®, unless the question requests a response based on a specific edition. This correspondence is not a formal interpretation of the NEC®. Any responses expressed to the questions are opinions and do not necessarily represent the official position of NECA, NFPA, or any technical committee. In addition, this correspondence is neither intended, nor should it be relied upon, to provide professional consultation or services.
ABOUT CHARLIE: Charles M. Trout, better known as Charlie, was a nationally known NEC® expert and author. He served on several NEC® technical committees and is past chairman of CMP-12. In 2006 Charlie was awarded the prestigious Coggeshall Award for outstanding contributions to the electrical contracting industry, codes and standards development, and technical training. Charlie was also a member of NECA’s Academy of Electrical Contracting. Charlie’s experienced team of industry experts keep the CQD dialogue and discussions active and informative in the spirit of the man himself, as he wanted.
NECA STANDARDS: NECA publishes the National Electrical Installation Standards™ (NEIS™), a series of ANSI-approved performance and quality standards for electrical construction. Visit NECA-NEIS.org for more information. NEISÃ” can be purchased in three formats: as paper books, on CD, or as electronic downloads.
NECA SAFETY PRODUCTS: NECA publishes valuable electrical safety books and CDs for the industry. Visit necanet.org/store to view or purchase NECA safety products.
CONTACT US: To submit a Code question, subscribe, or unsubscribe from this list, please e-mail: email@example.com.
© 1999 – 2014 National Electrical Installation Standards. All rights reserved.
Brought to you by NECA. NECA is the voice of the electrical contracting industry NATIONAL ELECTRICAL INSTALLATION STANDARDS, NEIS and the NEIS logo are registered trademarks of the National Electrical Contractors Association.
Created by Matrix Group International, Inc.