Standards as High as Your Own
NECA Online Help Desk Please leave a message
Re: CQD answer published Friday, October 26, 2018 -Flexible Cord Above Ceilings 3
In regards of the above ceiling appliances or equipment, I run into this by manufacturer directions for the installation of a condensate pump for a HVAC unit: “The pump shall be provided with a 6 ft. long TFE Teflon Â® insulated (450 °C) power cord. The all-metal condensate pump meets most local codes for certification as a “plenum rated“ pump for ceiling plenum installations.”
So, Can I have a receptacle above ceiling for the pump or hard wire to a switch? Or should I ask the Mechanical to specify that the pump is powered by the equipment itself?
By the way, thank you for your consistency with the emails it helps us all to keep up with the code.
Hey Camilo thanks for your follow up question and the compliment. Flexible cords, including power supply cords (usually with attachment plugs) are not allowed above suspended or dropped ceilings as stated in 400.12(5). A condensate pump with a power supply cord can be used for some applications but not if the flexible cord is above a suspended or dropped ceiling. TFE (tetrafluoroetheylene) insulation is usually used for high temperature applications and is included as one of the Z type insulations in Table 402 but 450 degrees C would be 842 degrees F.
If the manufacturer's instructions specifically state the pump and flexible curd are suitable for installation above a suspended or dropped ceiling ask them how that complies with 400.12(5). You didn't mention whether the condensate pump was listed but if it is check with the specific laboratory that listed it. Condensate pumps are available in versions that can be direct (hard) wired using a NEC Chapter 3 wiring method that is suitable for that location.
ABOUT CQD: NECA’s Code Question of the Day (CQD) is a leading National Electrical Code® forum for NECA and the industry. The CQD generates a lively dialogue and relative practical and Code-based responses to an ever-increasing and interactive audience.
IMPORTANT NOTICE: All answers are based on the latest edition of the National Electrical Code®, unless the question requests a response based on a specific edition. This correspondence is not a formal interpretation of the NEC®. Any responses expressed to the questions are opinions and do not necessarily represent the official position of NECA, NFPA, or any technical committee. In addition, this correspondence is neither intended, nor should it be relied upon, to provide professional consultation or services.
ABOUT CHARLIE: Charles M. Trout, better known as Charlie, was a nationally known NEC® expert and author. He served on several NEC® technical committees and is past chairman of CMP-12. In 2006 Charlie was awarded the prestigious Coggeshall Award for outstanding contributions to the electrical contracting industry, codes and standards development, and technical training. Charlie was also a member of NECA’s Academy of Electrical Contracting. Charlie’s experienced team of industry experts keep the CQD dialogue and discussions active and informative in the spirit of the man himself, as he wanted.
NECA STANDARDS: NECA publishes the National Electrical Installation Standards™ (NEIS™), a series of ANSI-approved performance and quality standards for electrical construction. Visit NECA-NEIS.org for more information. NEISÃ” can be purchased in three formats: as paper books, on CD, or as electronic downloads.
NECA SAFETY PRODUCTS: NECA publishes valuable electrical safety books and CDs for the industry. Visit necanet.org/store to view or purchase NECA safety products.
CONTACT US: To submit a Code question, subscribe, or unsubscribe from this list, please e-mail: firstname.lastname@example.org.
© 1999 – 2014 National Electrical Installation Standards. All rights reserved.
Brought to you by NECA. NECA is the voice of the electrical contracting industry NATIONAL ELECTRICAL INSTALLATION STANDARDS, NEIS and the NEIS logo are registered trademarks of the National Electrical Contractors Association.
Created by Matrix Group International, Inc.