Standards as High as Your Own
NECA Online Help Desk Please leave a message
Charlie Trout Flashback Question:
Our company does quite a bit of work for "places of assembly." We often find that older structures were often wired by methods that the current NEC does not allow, most often nonmetallic sheathed cable. Generally, we will use Type NM cable when doing repair work or making small additions to such buildings. I have been told that such work is permissible, being “grandfathered” under the Code that existed when the building was constructed. Evidently, the inspectors agree because our work was never been turned down for improper wiring methods. Is there any wording in the NEC that allows this, or is this permission given through national or local building codes?
Charlie Trout Flashback Answer:
Nonmetallic-sheathed cable is permitted in 518.4(B) to be used only in buildings or portions thereof that are not required to be of fire-rated construction by the applicable building code. The NEC has been consistent in this requirement prior to the acceptance of Article 518 into the 1975 NEC; this requirement was previously a part of Article 520, which at that time included Assembly Halls. The use of nonmetallic-sheathed cable has never been intended or permitted by the NEC in places of assembly except as shown above. Local requirements may differ from NEC requirements, but violations of the NEC should never be grandfathered in. See NEC Section 518.4(B).
ABOUT CQD: The Code Question of the Day (CQD) is NECA and ELECTRICAL CONTRACTOR Magazine’s flagship National Electrical Code (NEC®) public forum for the industry, sponsored by EATON. The daily distribution of Q&A generates a lively dialogue and shares relative Code-based practical responses.
SUBMIT YOUR CODE QUESTION: Click here to submit a question to for inclusion in an upcoming edition of the Code Question of the Day, or email email@example.com.
CHARLIE TROUT: Charles M. Trout, better known as Charlie, was a nationally known NEC® expert and author. He served on several NEC® technical committees and is past chairman of CMP-12. In 2006 Charlie was awarded the prestigious Coggeshall Award for outstanding contributions to the electrical contracting industry, codes and standards development, and technical training. Even though Charlie passed away in October of 2015, his work continues in spirit. NECA continues to maintain this question forum for its many subscribers in memory and recognition of all his significant contributions to making the NEC what it is today.
NECA STANDARDS: NECA publishes the National Electrical Installation Standards™ (NEIS™), a series of ANSI-approved performance and quality standards for electrical construction. NEIS can be purchased in the NECA Store in three formats: a printed or PDF download of a standard or, as an annual subscription service.
NECA SAFETY PRODUCTS & PUBLICATIONS: NECA produces electrical safety publications and products for the industry including jobsite safety guides, handbooks and resource kits. View a full listing of available resources and products »
IMPORTANT NOTICE: Unless the question requests a response based on a specific edition, all answers are based on the latest edition of NFPA 70® National Electrical Code®.
This correspondence is not a formal interpretation of the NEC® and any responses expressed to the questions are opinions and do not necessarily represent the official position of NECA, NFPA, the NEC Correlating Committee any Code-making panel or other electrical technical committee. In addition, this correspondence is neither intended, nor should it be relied upon, to provide professional consultation or services.
UPDATE YOUR SUBSCRIPTION PREFERENCES: Subscribe or Unsubscribe from this list.
© 1999 – 2014 National Electrical Installation Standards. All rights reserved.
Brought to you by NECA. NECA is the voice of the electrical contracting industry NATIONAL ELECTRICAL INSTALLATION STANDARDS, NEIS and the NEIS logo are registered trademarks of the National Electrical Contractors Association.
Created by Matrix Group International, Inc.