Standards as High as Your Own
NECA Online Help Desk Please leave a message
Re: CQD answer published Thursday, September 28, 2017 -Number of Ground Rods
Regarding the answer to today's CQD, here's the "Rest of the Story'". The second sentence of 250.50 states, "Where none of these grounding electrodes exist, one or more of the grounding electrodes specifed in 250.52(A)(4) through (A)(8) shall be installed and used."
Rod-type grounding electrodes are included in 250.52(A)(5). Two ground rods are required according to 250.53(A)(3) unless one ground rod has a resistance to earth of 25 ohms or less as provided in the Exception. Then, one ground rod is permitted.
This writer is aware that some AHJs permit only one ground rod to be installed for temporary services so the installer should verify what the local enforcement practices are.
Hey Phil thanks for your comment, that should have been included in the original answer and it is no surprise that you would notice given all your experience. As you point out if a ground rod is the only type of grounding electrode used then it must have a resistance to ground of 25 ohms or less. If not then an additional electrode is required and it is common to use a second ground rod. This applies even for temporary wiring because nothing in Article 590 changes the rule as stated in 590.2(A).
ABOUT CQD: NECA’s Code Question of the Day (CQD) is a leading National Electrical Code® forum for NECA and the industry. The CQD generates a lively dialogue and relative practical and Code-based responses to an ever-increasing and interactive audience.
IMPORTANT NOTICE: All answers are based on the latest edition of the National Electrical Code®, unless the question requests a response based on a specific edition. This correspondence is not a formal interpretation of the NEC®. Any responses expressed to the questions are opinions and do not necessarily represent the official position of NECA, NFPA, or any technical committee. In addition, this correspondence is neither intended, nor should it be relied upon, to provide professional consultation or services.
ABOUT CHARLIE: Charles M. Trout, better known as Charlie, was a nationally known NEC® expert and author. He served on several NEC® technical committees and is past chairman of CMP-12. In 2006 Charlie was awarded the prestigious Coggeshall Award for outstanding contributions to the electrical contracting industry, codes and standards development, and technical training. Charlie was also a member of NECA’s Academy of Electrical Contracting. Charlie’s experienced team of industry experts keep the CQD dialogue and discussions active and informative in the spirit of the man himself, as he wanted.
NECA STANDARDS: NECA publishes the National Electrical Installation Standards™ (NEIS™), a series of ANSI-approved performance and quality standards for electrical construction. Visit NECA-NEIS.org for more information. NEISÃ” can be purchased in three formats: as paper books, on CD, or as electronic downloads.
NECA SAFETY PRODUCTS: NECA publishes valuable electrical safety books and CDs for the industry. Visit necanet.org/store to view or purchase NECA safety products.
CONTACT US: To submit a Code question, subscribe, or unsubscribe from this list, please e-mail: firstname.lastname@example.org.
© 1999 – 2014 National Electrical Installation Standards. All rights reserved.
Brought to you by NECA. NECA is the voice of the electrical contracting industry NATIONAL ELECTRICAL INSTALLATION STANDARDS, NEIS and the NEIS logo are registered trademarks of the National Electrical Contractors Association.
Created by Matrix Group International, Inc.