Standards as High as Your Own
NECA Online Help Desk Please leave a message
Good morning. My question is regarding a "single "receptacle on an "individual "branch circuit. If I infer this particular section correctly, it allows the installer to use an ampere rating not LESS than the actual branch circuit used. So if I have a 15 amp circuit and am using a 30 amp 240 Volt receptacle (L6)it's code compliant. It feeds a PDU with a L6P(6 amps per leg).Keep in mind this is an individual branch circuit with a single receptacle NOT two or more receptacles. The inspector is saying it must be a 30 amp circuit even on an individual circuit. Am I wrong?
Your thoughts, Edward LoGatto
Hey Edward thanks for your question. If I understand your example you are correct. A single receptacle must have an ampere rating at least equal to that of the branch circuit as stated in 210.21(B)(1). Using a higher rated receptacle is not prohibited. See the definitions of Branch Circuit, Individual and Receptacle in Article 100. Make sure you are complying with any instructions included with the equipment if it is listed as stated in 110.3(B).
ABOUT CQD: NECA’s Code Question of the Day (CQD) is a leading National Electrical Code® forum for NECA and the industry. The CQD generates a lively dialogue and relative practical and Code-based responses to an ever-increasing and interactive audience.
IMPORTANT NOTICE: All answers are based on the latest edition of the National Electrical Code®, unless the question requests a response based on a specific edition. This correspondence is not a formal interpretation of the NEC®. Any responses expressed to the questions are opinions and do not necessarily represent the official position of NECA, NFPA, or any technical committee. In addition, this correspondence is neither intended, nor should it be relied upon, to provide professional consultation or services.
ABOUT CHARLIE: Charles M. Trout, better known as Charlie, was a nationally known NEC® expert and author. He served on several NEC® technical committees and is past chairman of CMP-12. In 2006 Charlie was awarded the prestigious Coggeshall Award for outstanding contributions to the electrical contracting industry, codes and standards development, and technical training. Charlie was also a member of NECA’s Academy of Electrical Contracting. Charlie’s experienced team of industry experts keep the CQD dialogue and discussions active and informative in the spirit of the man himself, as he wanted.
NECA STANDARDS: NECA publishes the National Electrical Installation Standards™ (NEIS™), a series of ANSI-approved performance and quality standards for electrical construction. Visit NECA-NEIS.org for more information. NEISÃ” can be purchased in three formats: as paper books, on CD, or as electronic downloads.
NECA SAFETY PRODUCTS: NECA publishes valuable electrical safety books and CDs for the industry. Visit necanet.org/store to view or purchase NECA safety products.
CONTACT US: To submit a Code question, subscribe, or unsubscribe from this list, please e-mail: firstname.lastname@example.org.
© 1999 – 2014 National Electrical Installation Standards. All rights reserved.
Brought to you by NECA. NECA is the voice of the electrical contracting industry NATIONAL ELECTRICAL INSTALLATION STANDARDS, NEIS and the NEIS logo are registered trademarks of the National Electrical Contractors Association.
Created by Matrix Group International, Inc.