Standards as High as Your Own
NECA Online Help Desk Please leave a message
Re: CQD answer published Wednesday, September 5, 2018 - Load Calculations
Load calculations per 220.83 existing building. I'm curious how additional loads should added?
I have been told by chief electrical inspectors at least 3 different ways.
1. Additional loads at 40%
2. Additional loads at 100%
3. Additional loads at 125%
I understand the misunderstanding. I've been told to use the 40% rule because that's what we'll be used the next time then additional loan is added.. makes sense. So I understanding the two other additional load calculations are extrapolated from other parts of the code book to make it more difficult to add additional loads to the existing structure? Are any of these methods correct or following the code as it is written? I am aware of how the rest of the calculation is done the first 10000 volt amps at 100% and the remainder at 40%. But the NEC does not specifically say additional loads at 40% or what percentage it should be added in at? Any help in this matter would be greatly appreciated. And as always Charlie thank you for the code question of the day and all of your great work answering our questions!
Thanks, Oliver Allen
Hey Oliver thanks for your question and the compliment. The answer to your question is found in the first sentences of 220.83(A) and (B) - "The following percentages shall be used for existing and additional new loads." For example, if no air conditioning or electric space heating loads are supplied the first 8 kVA of existing and proposed new loads are taken at 100 % and the remainder at 40% as stated in 220.83(A). If air conditioning or electric space heating loads are supplied the percentages in 220.83(B) are used.
ABOUT CQD: NECA’s Code Question of the Day (CQD) is a leading National Electrical Code® forum for NECA and the industry. The CQD generates a lively dialogue and relative practical and Code-based responses to an ever-increasing and interactive audience.
IMPORTANT NOTICE: All answers are based on the latest edition of the National Electrical Code®, unless the question requests a response based on a specific edition. This correspondence is not a formal interpretation of the NEC®. Any responses expressed to the questions are opinions and do not necessarily represent the official position of NECA, NFPA, or any technical committee. In addition, this correspondence is neither intended, nor should it be relied upon, to provide professional consultation or services.
ABOUT CHARLIE: Charles M. Trout, better known as Charlie, was a nationally known NEC® expert and author. He served on several NEC® technical committees and is past chairman of CMP-12. In 2006 Charlie was awarded the prestigious Coggeshall Award for outstanding contributions to the electrical contracting industry, codes and standards development, and technical training. Charlie was also a member of NECA’s Academy of Electrical Contracting. Charlie’s experienced team of industry experts keep the CQD dialogue and discussions active and informative in the spirit of the man himself, as he wanted.
NECA STANDARDS: NECA publishes the National Electrical Installation Standards™ (NEIS™), a series of ANSI-approved performance and quality standards for electrical construction. Visit NECA-NEIS.org for more information. NEISÃ” can be purchased in three formats: as paper books, on CD, or as electronic downloads.
NECA SAFETY PRODUCTS: NECA publishes valuable electrical safety books and CDs for the industry. Visit necanet.org/store to view or purchase NECA safety products.
CONTACT US: To submit a Code question, subscribe, or unsubscribe from this list, please e-mail: email@example.com.
© 1999 – 2014 National Electrical Installation Standards. All rights reserved.
Brought to you by NECA. NECA is the voice of the electrical contracting industry NATIONAL ELECTRICAL INSTALLATION STANDARDS, NEIS and the NEIS logo are registered trademarks of the National Electrical Contractors Association.
Created by Matrix Group International, Inc.