Standards as High as Your Own
NECA Online Help Desk Please leave a message
Hello Code Friends,
Do I need two grounding rods for a 100 ampere sub panel in my garage which will be used for feeding motor for a above ground pool.
There is not much information provided in the question that indicates where the panel is installed, or if it is installed in a single building supplied by a service or the panelboard is installed at a separate building or structure. It is difficult to read into what is being asked, but we'll give it a shot. If the panelboard is installed at a separate building and is the first disconnecting means for that separate structure as required by Section 225.31 and 225.32. Section 250.32(A) contains requirements for grounding electrodes at separate buildings or structures. All grounding electrodes present at the separate building or structure served shall be used to form the grounding electrode system. If no electrodes are present, then one shall be installed. If ground rods are chosen to be installed, then two must be installed unless a single ground rod does not exceed 25 ohms resistance to ground. See 250.53(A)(2) and the exception as applicable. If the panelboard is not in a separate building or structure, then the motor must be connected to an equipment grounding conductor of the branch circuit supplying the motor. The general equipment grounding requirements for motors of all voltages are are provided in Part XIII of Article 430. This part of Article 430 refers to the applicable sections within Article 250.
ABOUT CQD: The Code Question of the Day (CQD) is NECA and ELECTRICAL CONTRACTOR Magazine’s flagship National Electrical Code (NEC®) public forum for the industry, sponsored by EATON. The daily distribution of Q&A generates a lively dialogue and shares relative Code-based practical responses.
SUBMIT YOUR CODE QUESTION: Click here to submit a question to for inclusion in an upcoming edition of the Code Question of the Day, or email firstname.lastname@example.org.
CHARLIE TROUT: Charles M. Trout, better known as Charlie, was a nationally known NEC® expert and author. He served on several NEC® technical committees and is past chairman of CMP-12. In 2006 Charlie was awarded the prestigious Coggeshall Award for outstanding contributions to the electrical contracting industry, codes and standards development, and technical training. Even though Charlie passed away in October of 2015, his work continues in spirit. NECA continues to maintain this question forum for its many subscribers in memory and recognition of all his significant contributions to making the NEC what it is today.
NECA STANDARDS: NECA publishes the National Electrical Installation Standards™ (NEIS™), a series of ANSI-approved performance and quality standards for electrical construction. NEIS can be purchased in the NECA Store in three formats: a printed or PDF download of a standard or, as an annual subscription service.
NECA SAFETY PRODUCTS & PUBLICATIONS: NECA produces electrical safety publications and products for the industry including jobsite safety guides, handbooks and resource kits. View a full listing of available resources and products »
IMPORTANT NOTICE: Unless the question requests a response based on a specific edition, all answers are based on the latest edition of NFPA 70® National Electrical Code®.
This correspondence is not a formal interpretation of the NEC® and any responses expressed to the questions are opinions and do not necessarily represent the official position of NECA, NFPA, the NEC Correlating Committee any Code-making panel or other electrical technical committee. In addition, this correspondence is neither intended, nor should it be relied upon, to provide professional consultation or services.
UPDATE YOUR SUBSCRIPTION PREFERENCES: Subscribe or Unsubscribe from this list.
© 1999 – 2014 National Electrical Installation Standards. All rights reserved.
Brought to you by NECA. NECA is the voice of the electrical contracting industry NATIONAL ELECTRICAL INSTALLATION STANDARDS, NEIS and the NEIS logo are registered trademarks of the National Electrical Contractors Association.
Created by Matrix Group International, Inc.