Standards as High as Your Own
NECA Online Help Desk Please leave a message
Re: CQD answers published August 9, 21, 29, & 30, 2018 -Service Equipment 5
One more response to the Wednesday, August 29, 2018 Q&A if you want to continue this discussion. It is interesting to note that the installation of an electric utility's meter does not service equipment make. The meter location normally constitutes the service point and if it located remote from the service, the meter installation may be looked upon as a "wide place in the conduit." In other words, a service disconnecting means and overcurrent protection is not required so three wires are all that is required to the service in the case of a 120/240V, 1Ø installation.
Take care, Charlie Eldridge | Consultant
Hey Charlie thanks for your comment, it's always good to hear from you. You make a good point that wasn't specifically stated. The utility meter location does not necessarily determine the service point. For a 120/240 single phase service three conductors can be installed TO the service equipment. A wise inspector once stated that a key word in the definition of Service equipment is "intended". The circuit breaker of fused switch that is intended to be the main control and cutoff of the supply is the service equipment. Conductors on the load side ate typically feeders. Hopefully that will end the discussion for a while.
ABOUT CQD: NECA’s Code Question of the Day (CQD) is a leading National Electrical Code® forum for NECA and the industry. The CQD generates a lively dialogue and relative practical and Code-based responses to an ever-increasing and interactive audience.
IMPORTANT NOTICE: All answers are based on the latest edition of the National Electrical Code®, unless the question requests a response based on a specific edition. This correspondence is not a formal interpretation of the NEC®. Any responses expressed to the questions are opinions and do not necessarily represent the official position of NECA, NFPA, or any technical committee. In addition, this correspondence is neither intended, nor should it be relied upon, to provide professional consultation or services.
ABOUT CHARLIE: Charles M. Trout, better known as Charlie, was a nationally known NEC® expert and author. He served on several NEC® technical committees and is past chairman of CMP-12. In 2006 Charlie was awarded the prestigious Coggeshall Award for outstanding contributions to the electrical contracting industry, codes and standards development, and technical training. Charlie was also a member of NECA’s Academy of Electrical Contracting. Charlie’s experienced team of industry experts keep the CQD dialogue and discussions active and informative in the spirit of the man himself, as he wanted.
NECA STANDARDS: NECA publishes the National Electrical Installation Standards™ (NEIS™), a series of ANSI-approved performance and quality standards for electrical construction. Visit NECA-NEIS.org for more information. NEISÃ” can be purchased in three formats: as paper books, on CD, or as electronic downloads.
NECA SAFETY PRODUCTS: NECA publishes valuable electrical safety books and CDs for the industry. Visit necanet.org/store to view or purchase NECA safety products.
CONTACT US: To submit a Code question, subscribe, or unsubscribe from this list, please e-mail: email@example.com.
© 1999 – 2014 National Electrical Installation Standards. All rights reserved.
Brought to you by NECA. NECA is the voice of the electrical contracting industry NATIONAL ELECTRICAL INSTALLATION STANDARDS, NEIS and the NEIS logo are registered trademarks of the National Electrical Contractors Association.
Created by Matrix Group International, Inc.