Standards as High as Your Own
NECA Online Help Desk Please leave a message
Re: CQD answer published August 13 & August 23, 2018-Grounded Conductor Terminations 3
I agree with your answer on this but would like to append it with the need to consider impedance-grounded system. They can have a neutral wire (although mostly delta), but it's not intentionally grounded. So, not all neutrals are necessarily solidly grounded. Since most applications of impedance grounding is industrial and vast majority of electricians are not, but residential and commercial, their in lies the issue of lack of familiarity. Since most NEC classes are geared to residential and commercial, it makes the less covered impedance-grounded system even more mysterious. Lastly, when I used to attend NEC classes and update sessions (now happily retired since 2004, but like to keep an oar in the water), the thing that was always impressed by instructors is that: "The NEC is not an instruction manual"! Electricians need to continuously learn new things as well as keep up with changes. Submitting change proposals to the NEC is always a great way to learn about an issue. Even if your idea is not adopted, the CMP will give you an explanation of why it was rejected, and that is often very valuable since it's almost like getting an interpretation. It's great you encourage that.
Best Regards, Nick Abbatiello
Hey Nick thanks for your comment. Impedance grounded systems are a type of grounded system. You are correct they are not solidly grounded based on the definition of Grounded, Solidly in Article 100. A lot can be learned by reading resolved Public Inputs and public Comments.
ABOUT CQD: NECA’s Code Question of the Day (CQD) is a leading National Electrical Code® forum for NECA and the industry. The CQD generates a lively dialogue and relative practical and Code-based responses to an ever-increasing and interactive audience.
IMPORTANT NOTICE: All answers are based on the latest edition of the National Electrical Code®, unless the question requests a response based on a specific edition. This correspondence is not a formal interpretation of the NEC®. Any responses expressed to the questions are opinions and do not necessarily represent the official position of NECA, NFPA, or any technical committee. In addition, this correspondence is neither intended, nor should it be relied upon, to provide professional consultation or services.
ABOUT CHARLIE: Charles M. Trout, better known as Charlie, was a nationally known NEC® expert and author. He served on several NEC® technical committees and is past chairman of CMP-12. In 2006 Charlie was awarded the prestigious Coggeshall Award for outstanding contributions to the electrical contracting industry, codes and standards development, and technical training. Charlie was also a member of NECA’s Academy of Electrical Contracting. Charlie’s experienced team of industry experts keep the CQD dialogue and discussions active and informative in the spirit of the man himself, as he wanted.
NECA STANDARDS: NECA publishes the National Electrical Installation Standards™ (NEIS™), a series of ANSI-approved performance and quality standards for electrical construction. Visit NECA-NEIS.org for more information. NEISÃ” can be purchased in three formats: as paper books, on CD, or as electronic downloads.
NECA SAFETY PRODUCTS: NECA publishes valuable electrical safety books and CDs for the industry. Visit necanet.org/store to view or purchase NECA safety products.
CONTACT US: To submit a Code question, subscribe, or unsubscribe from this list, please e-mail: email@example.com.
© 1999 – 2014 National Electrical Installation Standards. All rights reserved.
Brought to you by NECA. NECA is the voice of the electrical contracting industry NATIONAL ELECTRICAL INSTALLATION STANDARDS, NEIS and the NEIS logo are registered trademarks of the National Electrical Contractors Association.
Created by Matrix Group International, Inc.