Standards as High as Your Own
NECA Online Help Desk Please leave a message
Re: CQD answer published August 9 & August 21, 2018 - Service Equipment 4
In response to the article debating whether a 3 wire single phase conductor set is allowed to a structure as opposed to 4 wire set, the petitioner referenced a " service pedestal" with an overcurrent device . We were all taught in apprenticeship any conductors on load side of an overcurrent device are feeders. Unfortunately this is only partially true. If this pedestal is installed and maintained by a serving utility, then the utility is responsible for declaring the "service point", as defined in NEC article 100 definitions as the point of demarcation where utility service ends and customer responsibility begins. The placement of an overcurrent device installed on the line side (utility) of a system does not render the conductors from said overcurrent device to the structure as feeders, but as service conductors if the utility declares the load side of the overcurrent device as the service point, which is the case with many utility supplied pedestals. This rendering of "service point" is completely the decision of the utility and not the NEC, nor any customer or other party. We can only declare "feeder" when and where the utility states it will be. Thank you much for this opportunity to clarify a greatly misunderstood area. Kelly Stockwill
Hey Kelly thanks for your comment. You are correct if the utility owns the disconnecting means at the pedestal then the service disconnecting means is downstream of that based on the definition of Service Point in article 100. The service overcurrent device must be located "at" the service disconnecting means location as stated in 230.91 but upstream overcurrent devices are not prohibited. Utilities are typically governed by regulatory commissions.
ABOUT CQD: NECA’s Code Question of the Day (CQD) is a leading National Electrical Code® forum for NECA and the industry. The CQD generates a lively dialogue and relative practical and Code-based responses to an ever-increasing and interactive audience.
IMPORTANT NOTICE: All answers are based on the latest edition of the National Electrical Code®, unless the question requests a response based on a specific edition. This correspondence is not a formal interpretation of the NEC®. Any responses expressed to the questions are opinions and do not necessarily represent the official position of NECA, NFPA, or any technical committee. In addition, this correspondence is neither intended, nor should it be relied upon, to provide professional consultation or services.
ABOUT CHARLIE: Charles M. Trout, better known as Charlie, was a nationally known NEC® expert and author. He served on several NEC® technical committees and is past chairman of CMP-12. In 2006 Charlie was awarded the prestigious Coggeshall Award for outstanding contributions to the electrical contracting industry, codes and standards development, and technical training. Charlie was also a member of NECA’s Academy of Electrical Contracting. Charlie’s experienced team of industry experts keep the CQD dialogue and discussions active and informative in the spirit of the man himself, as he wanted.
NECA STANDARDS: NECA publishes the National Electrical Installation Standards™ (NEIS™), a series of ANSI-approved performance and quality standards for electrical construction. Visit NECA-NEIS.org for more information. NEISÃ” can be purchased in three formats: as paper books, on CD, or as electronic downloads.
NECA SAFETY PRODUCTS: NECA publishes valuable electrical safety books and CDs for the industry. Visit necanet.org/store to view or purchase NECA safety products.
CONTACT US: To submit a Code question, subscribe, or unsubscribe from this list, please e-mail: firstname.lastname@example.org.
© 1999 – 2014 National Electrical Installation Standards. All rights reserved.
Brought to you by NECA. NECA is the voice of the electrical contracting industry NATIONAL ELECTRICAL INSTALLATION STANDARDS, NEIS and the NEIS logo are registered trademarks of the National Electrical Contractors Association.
Created by Matrix Group International, Inc.