Standards as High as Your Own
NECA Online Help Desk Please leave a message
Re: CQD answer published August 9 & August 21, 2018 - Service Equipment 3
Discussion on a main disconnect located at a remote pedestal feeding a home. Your answer was that the service is at the pedestal and a feeder would then supply the home and a 4 wire feeder circuit would be needed. My question how we ground this after we install the bonding jumper. There is no concrete encased ground at the pedestal. So does this then not need a concrete encased ground? Also the interconnect bonding bar needs to be installed at the service location. There will be very little use for those bonding bar at a remote pedestal. I'm not sure that a run of a fifth wire back to the home to make these connections could create a situation of a potential difference between the ground and the service. Curious what you think.
Hey Rod thanks for your follow up question. A grounding electrode conductor connection must be made at the service as stated in 250.24(A). A concreate encased electrode is not specifically required at a service but some type of grounding electrode is - as sated in 250.50.
A main bonding jumper must be installed in the service disconnect enclosure as stated in 250.24(B). It provides the path for ground fault current from the equipment grounding conductor (s) to the grounded (likely also a neutral conductor) conductor which is connected to the utility transformer. The grounded conductor can not be reconnected to ground at the load end of the feeder as started in 250.24(A)(5). This is to avoid objectionable current as stated in 240.6. An equipment grounding conductor must be connected to the service equipment and extend to a panelboard supplied from it.
ABOUT CQD: NECA’s Code Question of the Day (CQD) is a leading National Electrical Code® forum for NECA and the industry. The CQD generates a lively dialogue and relative practical and Code-based responses to an ever-increasing and interactive audience.
IMPORTANT NOTICE: All answers are based on the latest edition of the National Electrical Code®, unless the question requests a response based on a specific edition. This correspondence is not a formal interpretation of the NEC®. Any responses expressed to the questions are opinions and do not necessarily represent the official position of NECA, NFPA, or any technical committee. In addition, this correspondence is neither intended, nor should it be relied upon, to provide professional consultation or services.
ABOUT CHARLIE: Charles M. Trout, better known as Charlie, was a nationally known NEC® expert and author. He served on several NEC® technical committees and is past chairman of CMP-12. In 2006 Charlie was awarded the prestigious Coggeshall Award for outstanding contributions to the electrical contracting industry, codes and standards development, and technical training. Charlie was also a member of NECA’s Academy of Electrical Contracting. Charlie’s experienced team of industry experts keep the CQD dialogue and discussions active and informative in the spirit of the man himself, as he wanted.
NECA STANDARDS: NECA publishes the National Electrical Installation Standards™ (NEIS™), a series of ANSI-approved performance and quality standards for electrical construction. Visit NECA-NEIS.org for more information. NEISÃ” can be purchased in three formats: as paper books, on CD, or as electronic downloads.
NECA SAFETY PRODUCTS: NECA publishes valuable electrical safety books and CDs for the industry. Visit necanet.org/store to view or purchase NECA safety products.
CONTACT US: To submit a Code question, subscribe, or unsubscribe from this list, please e-mail: firstname.lastname@example.org.
© 1999 – 2014 National Electrical Installation Standards. All rights reserved.
Brought to you by NECA. NECA is the voice of the electrical contracting industry NATIONAL ELECTRICAL INSTALLATION STANDARDS, NEIS and the NEIS logo are registered trademarks of the National Electrical Contractors Association.
Created by Matrix Group International, Inc.