Standards as High as Your Own
NECA Online Help Desk Please leave a message
Re: CQD answer published Tuesday, August 14, 2018 - Feeder and Service Neutral Size
Charlie, I very much enjoy the CQD and start each of my days with reading the questions and answers. This is a very valuable forum for the industry.
Regarding the answer provided for the sizing of the neutral for dwelling services, the 2017 NEC does not allow the reduced neutral to be used for single phase 208/120 volt services or feeders from a 208/120 three-phase system. Small nuance in the text that has to be read carefully. 310.15(B)(7)(1) to (4) applies for 240/120 volt services, but only 310.15(B)(7)(1) to (3) apply to 208/120 volt services. The list item 4 is where the neutral is allowed to be reduced.
Keep up the good work, Chuck Mello
Hey Chuck it's good to hear from you. Thanks for your comment, the kind words, and for letting me off gently. You are correct. Only the neutrals of single phase services and feeders supplied from 120/240-volt systems are allowed to be sized using 310.15(B)(7)(4). The reference in the second paragraph was changed after the First Draft Report by Second Revision 1505 which included the following statement:
"The 208Y/120-volt application is limited to (1) through (3) due to the fact that the neutral of that system is a current-carrying conductor and must always be full sized in accordance with 220.61, and therefore the reduced neutral sizing allowed by (4) can never be applied."
ABOUT CQD: NECA’s Code Question of the Day (CQD) is a leading National Electrical Code® forum for NECA and the industry. The CQD generates a lively dialogue and relative practical and Code-based responses to an ever-increasing and interactive audience.
IMPORTANT NOTICE: All answers are based on the latest edition of the National Electrical Code®, unless the question requests a response based on a specific edition. This correspondence is not a formal interpretation of the NEC®. Any responses expressed to the questions are opinions and do not necessarily represent the official position of NECA, NFPA, or any technical committee. In addition, this correspondence is neither intended, nor should it be relied upon, to provide professional consultation or services.
ABOUT CHARLIE: Charles M. Trout, better known as Charlie, was a nationally known NEC® expert and author. He served on several NEC® technical committees and is past chairman of CMP-12. In 2006 Charlie was awarded the prestigious Coggeshall Award for outstanding contributions to the electrical contracting industry, codes and standards development, and technical training. Charlie was also a member of NECA’s Academy of Electrical Contracting. Charlie’s experienced team of industry experts keep the CQD dialogue and discussions active and informative in the spirit of the man himself, as he wanted.
NECA STANDARDS: NECA publishes the National Electrical Installation Standards™ (NEIS™), a series of ANSI-approved performance and quality standards for electrical construction. Visit NECA-NEIS.org for more information. NEISÃ” can be purchased in three formats: as paper books, on CD, or as electronic downloads.
NECA SAFETY PRODUCTS: NECA publishes valuable electrical safety books and CDs for the industry. Visit necanet.org/store to view or purchase NECA safety products.
CONTACT US: To submit a Code question, subscribe, or unsubscribe from this list, please e-mail: firstname.lastname@example.org.
© 1999 – 2014 National Electrical Installation Standards. All rights reserved.
Brought to you by NECA. NECA is the voice of the electrical contracting industry NATIONAL ELECTRICAL INSTALLATION STANDARDS, NEIS and the NEIS logo are registered trademarks of the National Electrical Contractors Association.
Created by Matrix Group International, Inc.