Standards as High as Your Own
NECA Online Help Desk Please leave a message
Re: CQD answer published Monday, August 13, 2018-Grounded Conductor Terminations 2
Grounded vs. grounding conductors..........
When is the NEC going to be written so it can be understood? 408.21 is a good example of how not to write the code. The attachment from Siemens recognized the problem and reverted to "neutral" and "ground" to explain the requirement.
Hey Dave thanks for your comment and for sharing the document with additional explanations based on the 2002 NEC. The section is now 408.41 in the 2017 NEC. The terms Neutral Conductor and Neutral Point were added in the 2008 NEC. A neutral conductor is connected to a system neutral point and is intended to carry current during normal conditions. Grounded Conductors are circuit or system conductors - that are intentionally grounded. Many neutral conductors are also grounded conductors but a grounded conductor supplied from a two wire system is not a neutral conductor. The NEC is often written in a manner that can cover various types of installations while still being technically correct. When white colored insulated conductors are called neutrals in the field, usually that is true but not always. If you have thoughts about revising the NEC wording so it is more understandable submit a Public Input or Public Comment to do that - it might help all of us.
ABOUT CQD: NECA’s Code Question of the Day (CQD) is a leading National Electrical Code® forum for NECA and the industry. The CQD generates a lively dialogue and relative practical and Code-based responses to an ever-increasing and interactive audience.
IMPORTANT NOTICE: All answers are based on the latest edition of the National Electrical Code®, unless the question requests a response based on a specific edition. This correspondence is not a formal interpretation of the NEC®. Any responses expressed to the questions are opinions and do not necessarily represent the official position of NECA, NFPA, or any technical committee. In addition, this correspondence is neither intended, nor should it be relied upon, to provide professional consultation or services.
ABOUT CHARLIE: Charles M. Trout, better known as Charlie, was a nationally known NEC® expert and author. He served on several NEC® technical committees and is past chairman of CMP-12. In 2006 Charlie was awarded the prestigious Coggeshall Award for outstanding contributions to the electrical contracting industry, codes and standards development, and technical training. Charlie was also a member of NECA’s Academy of Electrical Contracting. Charlie’s experienced team of industry experts keep the CQD dialogue and discussions active and informative in the spirit of the man himself, as he wanted.
NECA STANDARDS: NECA publishes the National Electrical Installation Standards™ (NEIS™), a series of ANSI-approved performance and quality standards for electrical construction. Visit NECA-NEIS.org for more information. NEISÃ” can be purchased in three formats: as paper books, on CD, or as electronic downloads.
NECA SAFETY PRODUCTS: NECA publishes valuable electrical safety books and CDs for the industry. Visit necanet.org/store to view or purchase NECA safety products.
CONTACT US: To submit a Code question, subscribe, or unsubscribe from this list, please e-mail: email@example.com.
© 1999 – 2014 National Electrical Installation Standards. All rights reserved.
Brought to you by NECA. NECA is the voice of the electrical contracting industry NATIONAL ELECTRICAL INSTALLATION STANDARDS, NEIS and the NEIS logo are registered trademarks of the National Electrical Contractors Association.
Created by Matrix Group International, Inc.