Standards as High as Your Own
NECA Online Help Desk Please leave a message
Re: CQD answer published Tuesday, August 7, 2018 -
Instead of using THHN conductors (I just assumed that since very popular), use a Machine Tool (MT) conductor with similar electrical properties but with finer strands of softer, or annealed, copper. The THHN and standard types of conductors are not designed for continuous flexing or significant vibratory motion because of stiffness. Machine tool wiring is designed for such applications. If that's not desired, a short length of outdoor rated type S flexible cord could be used. Type SWO comes to mind, but there are many others that even have better environmental ratings.
Hey Nick thanks for your comment, it's good to hear from you. An installation on a roof would be considered a wet location as that term is defined in Article 100 (Location, Wet). Conductors inside raceways above grade that are in wet locations must be suitable for wet locations as stated in 300.9 and comply with 310.15(C). Conductors that are only marked THHN are only suitable for dry and damp locations as shown in the application provisions column of Table 310.104. Many conductors marked THHN are also marked with insulation types that have a "W".
Machine tool wiring is intended to be used for machine tools as shown in the application provisions column of Table 310.104. The Informational Note references NFPA 79.
Flexible cords could be used as an alternative as stated in 400.10(A)(7) but also need a "W" as part of the marking as shown in the Use column of Table 400.4.
ABOUT CQD: NECA’s Code Question of the Day (CQD) is a leading National Electrical Code® forum for NECA and the industry. The CQD generates a lively dialogue and relative practical and Code-based responses to an ever-increasing and interactive audience.
IMPORTANT NOTICE: All answers are based on the latest edition of the National Electrical Code®, unless the question requests a response based on a specific edition. This correspondence is not a formal interpretation of the NEC®. Any responses expressed to the questions are opinions and do not necessarily represent the official position of NECA, NFPA, or any technical committee. In addition, this correspondence is neither intended, nor should it be relied upon, to provide professional consultation or services.
ABOUT CHARLIE: Charles M. Trout, better known as Charlie, was a nationally known NEC® expert and author. He served on several NEC® technical committees and is past chairman of CMP-12. In 2006 Charlie was awarded the prestigious Coggeshall Award for outstanding contributions to the electrical contracting industry, codes and standards development, and technical training. Charlie was also a member of NECA’s Academy of Electrical Contracting. Charlie’s experienced team of industry experts keep the CQD dialogue and discussions active and informative in the spirit of the man himself, as he wanted.
NECA STANDARDS: NECA publishes the National Electrical Installation Standards™ (NEIS™), a series of ANSI-approved performance and quality standards for electrical construction. Visit NECA-NEIS.org for more information. NEISÃ” can be purchased in three formats: as paper books, on CD, or as electronic downloads.
NECA SAFETY PRODUCTS: NECA publishes valuable electrical safety books and CDs for the industry. Visit necanet.org/store to view or purchase NECA safety products.
CONTACT US: To submit a Code question, subscribe, or unsubscribe from this list, please e-mail: firstname.lastname@example.org.
© 1999 – 2014 National Electrical Installation Standards. All rights reserved.
Brought to you by NECA. NECA is the voice of the electrical contracting industry NATIONAL ELECTRICAL INSTALLATION STANDARDS, NEIS and the NEIS logo are registered trademarks of the National Electrical Contractors Association.
Created by Matrix Group International, Inc.