Standards as High as Your Own
NECA Online Help Desk Please leave a message
Good morning to all of you, my name it's Eduardo M. I have a question regarding table 250.122, minimum size equipment grounding conductor, on the column of rating or settings in amperes 30,40,50,70,80, and so on it's missing the size. My question it's for an example what size would be on awg if I use for, 30,40, and 50 amperes, can you explain, thanks and I appreciate your patience.
Hey Eduardo thanks for your question. The last words in the heading of the first column in Table 250.122 are "Not Exceeding". For overcurrent device ratings or settings of 30, 40 or 50 amperes, those values exceed the 20 value in the first column so you have to go up to the 60 value resulting in a 10 AWG copper or 8 AWG aluminum conductor. The 10 AWG copper or 8 AWG aluminum would be the minimum size allowed for anything above 20 amperes up to 60 amperes. A change to remove some of those intermediate values was made in the 2011 NEC.
ABOUT CQD: NECA’s Code Question of the Day (CQD) is a leading National Electrical Code® forum for NECA and the industry. The CQD generates a lively dialogue and relative practical and Code-based responses to an ever-increasing and interactive audience.
IMPORTANT NOTICE: All answers are based on the latest edition of the National Electrical Code®, unless the question requests a response based on a specific edition. This correspondence is not a formal interpretation of the NEC®. Any responses expressed to the questions are opinions and do not necessarily represent the official position of NECA, NFPA, or any technical committee. In addition, this correspondence is neither intended, nor should it be relied upon, to provide professional consultation or services.
ABOUT CHARLIE: Charles M. Trout, better known as Charlie, was a nationally known NEC® expert and author. He served on several NEC® technical committees and is past chairman of CMP-12. In 2006 Charlie was awarded the prestigious Coggeshall Award for outstanding contributions to the electrical contracting industry, codes and standards development, and technical training. Charlie was also a member of NECA’s Academy of Electrical Contracting. Charlie’s experienced team of industry experts keep the CQD dialogue and discussions active and informative in the spirit of the man himself, as he wanted.
NECA STANDARDS: NECA publishes the National Electrical Installation Standards™ (NEIS™), a series of ANSI-approved performance and quality standards for electrical construction. Visit NECA-NEIS.org for more information. NEISÃ” can be purchased in three formats: as paper books, on CD, or as electronic downloads.
NECA SAFETY PRODUCTS: NECA publishes valuable electrical safety books and CDs for the industry. Visit necanet.org/store to view or purchase NECA safety products.
CONTACT US: To submit a Code question, subscribe, or unsubscribe from this list, please e-mail: firstname.lastname@example.org.
© 1999 – 2014 National Electrical Installation Standards. All rights reserved.
Brought to you by NECA. NECA is the voice of the electrical contracting industry NATIONAL ELECTRICAL INSTALLATION STANDARDS, NEIS and the NEIS logo are registered trademarks of the National Electrical Contractors Association.
Created by Matrix Group International, Inc.