Standards as High as Your Own
NECA Online Help Desk Please leave a message
Good morning to all of you, my name it's Eduardo M. I have a question regarding table 250.122, minimum size equipment grounding conductor, on the column of rating or settings in amperes 30,40,50,70,80, and so on it's missing the size. My question it's for an example what size would be on awg if I use for, 30,40, and 50 amperes, can you explain, thanks and I appreciate your patience.
Hey Eduardo thanks for your question. The last words in the heading of the first column in Table 250.122 are "Not Exceeding". For overcurrent device ratings or settings of 30, 40 or 50 amperes, those values exceed the 20 value in the first column so you have to go up to the 60 value resulting in a 10 AWG copper or 8 AWG aluminum conductor. The 10 AWG copper or 8 AWG aluminum would be the minimum size allowed for anything above 20 amperes up to 60 amperes. A change to remove some of those intermediate values was made in the 2011 NEC.
ABOUT CQD: The Code Question of the Day (CQD) is NECA and ELECTRICAL CONTRACTOR Magazine’s flagship National Electrical Code (NEC®) public forum for the industry, sponsored by EATON. The daily distribution of Q&A generates a lively dialogue and shares relative Code-based practical responses.
SUBMIT YOUR CODE QUESTION: Click here to submit a question to for inclusion in an upcoming edition of the Code Question of the Day, or email email@example.com.
CHARLIE TROUT: Charles M. Trout, better known as Charlie, was a nationally known NEC® expert and author. He served on several NEC® technical committees and is past chairman of CMP-12. In 2006 Charlie was awarded the prestigious Coggeshall Award for outstanding contributions to the electrical contracting industry, codes and standards development, and technical training. Even though Charlie passed away in October of 2015, his work continues in spirit. NECA continues to maintain this question forum for its many subscribers in memory and recognition of all his significant contributions to making the NEC what it is today.
NECA STANDARDS: NECA publishes the National Electrical Installation Standards™ (NEIS™), a series of ANSI-approved performance and quality standards for electrical construction. NEIS can be purchased in the NECA Store in three formats: a printed or PDF download of a standard or, as an annual subscription service.
NECA SAFETY PRODUCTS & PUBLICATIONS: NECA produces electrical safety publications and products for the industry including jobsite safety guides, handbooks and resource kits. View a full listing of available resources and products »
IMPORTANT NOTICE: Unless the question requests a response based on a specific edition, all answers are based on the latest edition of NFPA 70® National Electrical Code®.
This correspondence is not a formal interpretation of the NEC® and any responses expressed to the questions are opinions and do not necessarily represent the official position of NECA, NFPA, the NEC Correlating Committee any Code-making panel or other electrical technical committee. In addition, this correspondence is neither intended, nor should it be relied upon, to provide professional consultation or services.
UPDATE YOUR SUBSCRIPTION PREFERENCES: Subscribe or Unsubscribe from this list.
© 1999 – 2014 National Electrical Installation Standards. All rights reserved.
Brought to you by NECA. NECA is the voice of the electrical contracting industry NATIONAL ELECTRICAL INSTALLATION STANDARDS, NEIS and the NEIS logo are registered trademarks of the National Electrical Contractors Association.
Created by Matrix Group International, Inc.