Standards as High as Your Own
NECA Online Help Desk Please leave a message
A 12" deep panel is flush mounted in a 8" block wall (Question #1: Allowed?). In the opposing room, there are (2) 6" conduits mounted to strut that has been fastened to the rear 4" of the panel that is sticking out of the wall, which leads to Q2, is mounting the strut to the back of the panel allowed? I found no such information on panels that stick through walls in the NEC, except possibly not a neat and workmanlike installation (110.12).
Thank you. John Kreider
Hey John thanks for your question. I believe you are referring to panelboards. Panelboards are actually the busses and overcurrent devices and are designed to be placed in a cabinet or cutout box against or in a wall as that term is defined in Article 100. Cabinets can be surface or flush mounted as they are defined in Article 100. Unless there is something in the listing instructions or a concern about the wall having a fire-resistant rating, the NEC does not specifically prohibit the cabinet from extending past the back side of the wall.
Raceways must be secured and supported as stated in 300.11 and by any requirements based on the specific raceway used in the .30 section of the applicable Article. Those rules restrict some things from being used for support but they do not specify what must be used to support the raceways. It is quite possible the installation is installed in a neat and workmanlike manner so even 110.12 might not apply. So a lot of words for it might not be a violation.
ABOUT CQD: The Code Question of the Day (CQD) is NECA and ELECTRICAL CONTRACTOR Magazine’s flagship National Electrical Code (NEC®) public forum for the industry, sponsored by EATON. The daily distribution of Q&A generates a lively dialogue and shares relative Code-based practical responses.
SUBMIT YOUR CODE QUESTION: Click here to submit a question to for inclusion in an upcoming edition of the Code Question of the Day, or email email@example.com.
CHARLIE TROUT: Charles M. Trout, better known as Charlie, was a nationally recognized NEC® expert and author. He served on several NEC technical committees and is past chairman of CMP-12. In 2006, Charlie was awarded NECA’s prestigious Coggeshall Award for outstanding contributions to the electrical contracting industry, codes and standards development and technical training. NECA continues to provide this public forum in memory and recognition of all his fine contributions that has made the NEC what it is today.
NECA STANDARDS: NECA publishes the National Electrical Installation Standards™ (NEIS™), a series of ANSI-approved performance and quality standards for electrical construction. NEIS can be purchased in the NECA Store in three formats: a printed or PDF download of a standard or, as an annual subscription service.
NECA SAFETY PRODUCTS & PUBLICATIONS: NECA produces electrical safety publications and products for the industry including jobsite safety guides, handbooks and resource kits. View a full listing of available resources and products »
IMPORTANT NOTICE: Unless the question requests a response based on a specific edition, all answers are based on the latest edition of NFPA 70® National Electrical Code®.
This correspondence is not a formal interpretation of the NEC® and any responses expressed to the questions are opinions and do not necessarily represent the official position of NECA, NFPA, the NEC Correlating Committee any Code-making panel or other electrical technical committee. In addition, this correspondence is neither intended, nor should it be relied upon, to provide professional consultation or services.
UPDATE YOUR SUBSCRIPTION PREFERENCES: Subscribe or Unsubscribe from this list.
© 1999 – 2014 National Electrical Installation Standards. All rights reserved.
Brought to you by NECA. NECA is the voice of the electrical contracting industry NATIONAL ELECTRICAL INSTALLATION STANDARDS, NEIS and the NEIS logo are registered trademarks of the National Electrical Contractors Association.
Created by Matrix Group International, Inc.