Standards as High as Your Own
NECA Online Help Desk Please leave a message
Thanks for the code-a-day. A fun way to start the morning! Lots of arguments and cups of coffee lost and won!
NEC 680.23(B)(1) does not require a wet-niche fixture to have provisions for a #8 ground if it is a listed low voltage lighting system. However, NEC 680.23(B)(2) still requires a pool rated junction box. It seems unnecessary if there is no # 8 pulled to the wet-niche fixture or any ground pulled to the wet-niche fixture. Am I reading the code correct?
Hey Mike thanks for your question, you have a good point, and we are glad to help start your day. As you state, forming shells used with nonmetallic conduit must include provisions for terminating the 8 AWG copper conductor - other than those listed as low voltage systems as stated in 680.21(B)(1). Conduit must be installed from the forming shell to a junction box or other enclosure complying with 680.24 as stated in 680.21(B)(2). The 8 AWG bonding conductor is not required in nonmetallic conduit if listed as low voltage systems are used also stated in 680.21(B)(2).
All metal forming shells are required to be bonded as stated in 680.26(B)(4) unless the exception applies for listed low voltage lighting systems with nonmetallic forming shells.
So, yes you are correct, it seems unnecessary to have the bonding terminations if all the stated conditions are met. It is possible that no one has submitted a PI to address this, and possible that UL 1241, Standard for Junction Boxes for Swimming Pool Luminaires does not allow for omitting the bonding termination. If any swimming pool equipment manufacturer or UL representative has any additional insight please send in a comment.
ABOUT CQD: NECA’s Code Question of the Day (CQD) is a leading National Electrical Code® forum for NECA and the industry. The CQD generates a lively dialogue and relative practical and Code-based responses to an ever-increasing and interactive audience.
IMPORTANT NOTICE: All answers are based on the latest edition of the National Electrical Code®, unless the question requests a response based on a specific edition. This correspondence is not a formal interpretation of the NEC®. Any responses expressed to the questions are opinions and do not necessarily represent the official position of NECA, NFPA, or any technical committee. In addition, this correspondence is neither intended, nor should it be relied upon, to provide professional consultation or services.
ABOUT CHARLIE: Charles M. Trout, better known as Charlie, was a nationally known NEC® expert and author. He served on several NEC® technical committees and is past chairman of CMP-12. In 2006 Charlie was awarded the prestigious Coggeshall Award for outstanding contributions to the electrical contracting industry, codes and standards development, and technical training. Charlie was also a member of NECA’s Academy of Electrical Contracting. Charlie’s experienced team of industry experts keep the CQD dialogue and discussions active and informative in the spirit of the man himself, as he wanted.
NECA STANDARDS: NECA publishes the National Electrical Installation Standards™ (NEIS™), a series of ANSI-approved performance and quality standards for electrical construction. Visit NECA-NEIS.org for more information. NEISÃ” can be purchased in three formats: as paper books, on CD, or as electronic downloads.
NECA SAFETY PRODUCTS: NECA publishes valuable electrical safety books and CDs for the industry. Visit necanet.org/store to view or purchase NECA safety products.
CONTACT US: To submit a Code question, subscribe, or unsubscribe from this list, please e-mail: email@example.com.
© 1999 – 2014 National Electrical Installation Standards. All rights reserved.
Brought to you by NECA. NECA is the voice of the electrical contracting industry NATIONAL ELECTRICAL INSTALLATION STANDARDS, NEIS and the NEIS logo are registered trademarks of the National Electrical Contractors Association.
Created by Matrix Group International, Inc.