Standards as High as Your Own
NECA Online Help Desk Please leave a message
Can you build an outdoor residential service with a meter can and EMT riser through the roof and have it all rocked in. In other words, standing in front of the service all you would see is the enclosure door of the load center and the Meter face, everything else including the 2" riser conduit would be behind the rock. My thought is that you can't do that but I can't find any code in the NEC that supports that? Please e-Mail me.
Hey Clayton thanks for your question. The service disconnecting means, if inside a building or structure, must be located nearest the point of entrance of the service conductors 230.70(A)(1). The purpose is to limit how much conductor length is inside a building because service conductors typically do not have upstream overcurrent protection at their ampacity. No specific length is given in the NEC for how much conductor is allowed inside the building so it is determined by the AHJ. Many would likely consider the conductors inside the wall as being inside the building. This issue also seems to be treated differently in various locations.
ABOUT CQD: The Code Question of the Day (CQD) is NECA and ELECTRICAL CONTRACTOR Magazine’s flagship National Electrical Code (NEC®) public forum for the industry, sponsored by EATON. The daily distribution of Q&A generates a lively dialogue and shares relative Code-based practical responses.
SUBMIT YOUR CODE QUESTION: Click here to submit a question to for inclusion in an upcoming edition of the Code Question of the Day, or email firstname.lastname@example.org.
CHARLIE TROUT: Charles M. Trout, better known as Charlie, was a nationally recognized NEC® expert and author. He served on several NEC technical committees and is past chairman of CMP-12. In 2006, Charlie was awarded NECA’s prestigious Coggeshall Award for outstanding contributions to the electrical contracting industry, codes and standards development and technical training. NECA continues to provide this public forum in memory and recognition of all his fine contributions that has made the NEC what it is today.
NECA STANDARDS: NECA publishes the National Electrical Installation Standards™ (NEIS™), a series of ANSI-approved performance and quality standards for electrical construction. NEIS can be purchased in the NECA Store in three formats: a printed or PDF download of a standard or, as an annual subscription service.
NECA SAFETY PRODUCTS & PUBLICATIONS: NECA produces electrical safety publications and products for the industry including jobsite safety guides, handbooks and resource kits. View a full listing of available resources and products »
IMPORTANT NOTICE: Unless the question requests a response based on a specific edition, all answers are based on the latest edition of NFPA 70® National Electrical Code®.
This correspondence is not a formal interpretation of the NEC® and any responses expressed to the questions are opinions and do not necessarily represent the official position of NECA, NFPA, the NEC Correlating Committee any Code-making panel or other electrical technical committee. In addition, this correspondence is neither intended, nor should it be relied upon, to provide professional consultation or services.
UPDATE YOUR SUBSCRIPTION PREFERENCES: Subscribe or Unsubscribe from this list.
© 1999 – 2014 National Electrical Installation Standards. All rights reserved.
Brought to you by NECA. NECA is the voice of the electrical contracting industry NATIONAL ELECTRICAL INSTALLATION STANDARDS, NEIS and the NEIS logo are registered trademarks of the National Electrical Contractors Association.
Created by Matrix Group International, Inc.