Standards as High as Your Own
NECA Online Help Desk Please leave a message
Dear CQD: Most of our manufacturing equipment is supplied by a 480V ungrounded delta system. The busways have only the three phase conductors, with no grounding conductor in the bus. The manufacturing equipment is "grounded" (?) by properly-sized equipment grounding conductors that are connected to field-installed ground lugs screwed to the metallic bus plug enclosures, using whatever type of machine screw and nut is handy (few of the bus plugs, if any, have a factory-installed grounding means in them). I don't know how the busway enclosure is grounded, but the bus plugs are clamped to the painted busway via painted clamps. Almost every machine comes from the build shop with a 120V duplex receptacle (sometimes GFCI protected), supplied by a 480V x 120V step-down transformer, and protected by a 10A or smaller OCPD (receptacle is intended for powering a programming terminal). The receptacle's ground wire AND grounded circuit conductor are both connected to the X2 of the transformer. In turn, the X2 of the transformer is connected to the backplane/enclosure of the manufacturing equipment. This is a very common arrangement is manufacturing plants.
With regard to grounding and bonding, what code violations come to mind with this type of installation, for both the 480V and 120V circuits described, if any?
Thanks, Wes Nichols
Hey Wes thanks for your question. You don't mention when the equipment was installed but many thoughts come to mind and here are a few of them.
For listed busways, the enclosures and, in some cases an additional ground bus, are intended for use as equipment grounding conductors as stated in Busways and Associated Fittings, CWFT.
Check your busway manufacturers literature, it that is available, or contact them if they are still in business to determine if the busway enclosure is intended to be used as an equipment grounding conductor.
A fault current path is required for ungrounded systems as stated in 250.4(B)(4). A requirement for ungrounded systems to have ground detectors was added in the 2005 NEC in 250.21. The rules in 250.8 and 250.12 might not have been the same when the installation was made but they are very important.
If you meet the conditions in 250.30(A)(1) Ex. No 3 and 250.30(A)(5) Ex. No 3 for Class 1 circuits, the 120 volt circuits might be acceptable.
Beyond the NEC, OSHA has some retroactive rules that can apply such as in 1910.304(g)(1)(ii), (g)(1)(iii), (g)(1)(iv), and (g)(1)(v) and 1910.304(g)(5).
Finally, when a fault occurs will people be exposed to hazards, that is a concern that should be considered.
ABOUT CQD: The Code Question of the Day (CQD) is NECA and ELECTRICAL CONTRACTOR Magazine’s flagship National Electrical Code (NEC®) public forum for the industry, sponsored by EATON. The daily distribution of Q&A generates a lively dialogue and shares relative Code-based practical responses.
SUBMIT YOUR CODE QUESTION: Click here to submit a question to for inclusion in an upcoming edition of the Code Question of the Day, or email firstname.lastname@example.org.
CHARLIE TROUT: Charles M. Trout, better known as Charlie, was a nationally recognized NEC® expert and author. He served on several NEC technical committees and is past chairman of CMP-12. In 2006, Charlie was awarded NECA’s prestigious Coggeshall Award for outstanding contributions to the electrical contracting industry, codes and standards development and technical training. NECA continues to provide this public forum in memory and recognition of all his fine contributions that has made the NEC what it is today.
NECA STANDARDS: NECA publishes the National Electrical Installation Standards™ (NEIS™), a series of ANSI-approved performance and quality standards for electrical construction. NEIS can be purchased in the NECA Store in three formats: a printed or PDF download of a standard or, as an annual subscription service.
NECA SAFETY PRODUCTS & PUBLICATIONS: NECA produces electrical safety publications and products for the industry including jobsite safety guides, handbooks and resource kits. View a full listing of available resources and products »
IMPORTANT NOTICE: Unless the question requests a response based on a specific edition, all answers are based on the latest edition of NFPA 70® National Electrical Code®.
This correspondence is not a formal interpretation of the NEC® and any responses expressed to the questions are opinions and do not necessarily represent the official position of NECA, NFPA, the NEC Correlating Committee any Code-making panel or other electrical technical committee. In addition, this correspondence is neither intended, nor should it be relied upon, to provide professional consultation or services.
UPDATE YOUR SUBSCRIPTION PREFERENCES: Subscribe or Unsubscribe from this list.
© 1999 – 2014 National Electrical Installation Standards. All rights reserved.
Brought to you by NECA. NECA is the voice of the electrical contracting industry NATIONAL ELECTRICAL INSTALLATION STANDARDS, NEIS and the NEIS logo are registered trademarks of the National Electrical Contractors Association.
Created by Matrix Group International, Inc.