Standards as High as Your Own
NECA Online Help Desk Please leave a message
Section 300.13(A) prohibits splices and taps within raceways. My question centers around a ceiling fan. In certain cases the height of a ceiling requires the fan to use a longer downrod than was originally supplied with the fan. Some downrods are 8' in length. Occasionally, the length of lead wire supplied with the fan is not long enough to span the entire length of the downrod. In these cases, if a connection/splice is made in the downrod, does it violate Section 300.13(A). I guess my basic question is, is the downrod considered a raceway?
Hey Bill thanks for your question. The definition of Raceway in Article 100 is sufficiently broad enough that a paddle fan "downrod" could be included. But it would likely not be included in any of the specific raceway types that are defined in the XXX.2 sections of Chapter 3. Splices are generally only allowed in raceways that have removable covers.
The "downrod" you are describing would also likely be part of the paddle fan "kit" or available as an accessory. Ideally the instructions with the fan, that are reviewed by the testing laboratory certifying the fan, would include the instructions for which fans are intended to be used with specific downrods or how they are to be installed.
Is the fan motor available with longer leads? Is there space in the fan assembly for splices to be made? If the fan instructions do not give specific instructions allowing splices in downrods it seems they would not be.
ABOUT CQD: NECA’s Code Question of the Day (CQD) is a leading National Electrical Code® forum for NECA and the industry. The CQD generates a lively dialogue and relative practical and Code-based responses to an ever-increasing and interactive audience.
IMPORTANT NOTICE: All answers are based on the latest edition of the National Electrical Code®, unless the question requests a response based on a specific edition. This correspondence is not a formal interpretation of the NEC®. Any responses expressed to the questions are opinions and do not necessarily represent the official position of NECA, NFPA, or any technical committee. In addition, this correspondence is neither intended, nor should it be relied upon, to provide professional consultation or services.
ABOUT CHARLIE: Charles M. Trout, better known as Charlie, was a nationally known NEC® expert and author. He served on several NEC® technical committees and is past chairman of CMP-12. In 2006 Charlie was awarded the prestigious Coggeshall Award for outstanding contributions to the electrical contracting industry, codes and standards development, and technical training. Charlie was also a member of NECA’s Academy of Electrical Contracting. Charlie’s experienced team of industry experts keep the CQD dialogue and discussions active and informative in the spirit of the man himself, as he wanted.
NECA STANDARDS: NECA publishes the National Electrical Installation Standards™ (NEIS™), a series of ANSI-approved performance and quality standards for electrical construction. Visit NECA-NEIS.org for more information. NEISÃ” can be purchased in three formats: as paper books, on CD, or as electronic downloads.
NECA SAFETY PRODUCTS: NECA publishes valuable electrical safety books and CDs for the industry. Visit necanet.org/store to view or purchase NECA safety products.
CONTACT US: To submit a Code question, subscribe, or unsubscribe from this list, please e-mail: firstname.lastname@example.org.
© 1999 – 2014 National Electrical Installation Standards. All rights reserved.
Brought to you by NECA. NECA is the voice of the electrical contracting industry NATIONAL ELECTRICAL INSTALLATION STANDARDS, NEIS and the NEIS logo are registered trademarks of the National Electrical Contractors Association.
Created by Matrix Group International, Inc.