Standards as High as Your Own
NECA Online Help Desk Please leave a message
I thought I knew how to wire transformers until a few days ago. There are some guys that say you don't need to bond the transformer to the building grounding electrode system when you aren't using the neutral on the secondary. Say when you have a 480 volt 3 phase 3 wire primary and a 208 volt 3 phase 3 wire secondary to some piece of manufacturing equipment or A/C unit. I have looked through the code book and asked several other electricians and haven't got any real substantial answers or code references. I talked to one person that mentioned the exception in 250.121. I tried to follow it through the code book and I still don't think I understand it. Please help me understand this and find me a code reference so that I can go back to the people asking me these questions and give them some answers. I hope I have explained my issue well enough and my terminology isn't to messed up. I have been reading Code question of the day for a couple of code cycles now and it has been a big help. Thank you for the forum.
Hey Vern thanks for your question and the kind words. The same thing happens to me a lot, thought I knew something then realized I didn't.
In your example the 208Y/120 volt transformer secondary needs to be grounded, even though the neutral conductor is not used, as stated in 250.20(B)(1). Separately Derived Systems, as that term is defined in Article 100 and which the transformer in your example very likely is, must be installed based on 250.30. The building grounding electrode system must be used as the grounding electrode for the transformer as stated in 250.30(A)(4). A grounding electrode conductor must be installed as stated in 250.30(A)(5) and be connected as stated in 250.68(C).
Any metal water piping systems and exposed structural metal building frames, in the area served, need to be bonded to the grounded conductor as stated in 250.104(D). That NEC wording probably needs to be improved because in your example there really is no grounded conductor other than the termination point (XO) - even though the system is grounded.
The exception to 250.121 allows a wire type equipment grounding conductor to also be used as a grounding electrode conductor if that conductor complies with the rules for both types of conductors.
ABOUT CQD: NECA’s Code Question of the Day (CQD) is a leading National Electrical Code® forum for NECA and the industry. The CQD generates a lively dialogue and relative practical and Code-based responses to an ever-increasing and interactive audience.
IMPORTANT NOTICE: All answers are based on the latest edition of the National Electrical Code®, unless the question requests a response based on a specific edition. This correspondence is not a formal interpretation of the NEC®. Any responses expressed to the questions are opinions and do not necessarily represent the official position of NECA, NFPA, or any technical committee. In addition, this correspondence is neither intended, nor should it be relied upon, to provide professional consultation or services.
ABOUT CHARLIE: Charles M. Trout, better known as Charlie, was a nationally known NEC® expert and author. He served on several NEC® technical committees and is past chairman of CMP-12. In 2006 Charlie was awarded the prestigious Coggeshall Award for outstanding contributions to the electrical contracting industry, codes and standards development, and technical training. Charlie was also a member of NECA’s Academy of Electrical Contracting. Charlie’s experienced team of industry experts keep the CQD dialogue and discussions active and informative in the spirit of the man himself, as he wanted.
NECA STANDARDS: NECA publishes the National Electrical Installation Standards™ (NEIS™), a series of ANSI-approved performance and quality standards for electrical construction. Visit NECA-NEIS.org for more information. NEISÃ” can be purchased in three formats: as paper books, on CD, or as electronic downloads.
NECA SAFETY PRODUCTS: NECA publishes valuable electrical safety books and CDs for the industry. Visit necanet.org/store to view or purchase NECA safety products.
CONTACT US: To submit a Code question, subscribe, or unsubscribe from this list, please e-mail: email@example.com.
© 1999 – 2014 National Electrical Installation Standards. All rights reserved.
Brought to you by NECA. NECA is the voice of the electrical contracting industry NATIONAL ELECTRICAL INSTALLATION STANDARDS, NEIS and the NEIS logo are registered trademarks of the National Electrical Contractors Association.
Created by Matrix Group International, Inc.