Standards as High as Your Own
NECA Online Help Desk Please leave a message
I read on a webpage that you consider a RV pedestal as a “separate structure” and must contain a ground rod to be driven at each location. However, my reading of what follows contradicts that. Can you let me know if I’m wrong?
The only equipment requiring grounding electrodes is the electrical service equipment. 250.54 contains permissive, but not required, language that allows for auxiliary grounding electrodes to be installed and connected to the equipment grounding conductor. Keep in mind that the pedestal is equipment, and NOT A STRUCTURE, so there are no NEC code requirements for having grounding electrodes on equipment that does not require them. Only equipment for separately derived systems and buildings or structures supplied by feeders or multiple branch circuits (other than multiwire) are required to have grounding electrodes.
Auxiliary electrodes serve no real purpose, you will have to have an equipment grounding conductor installed with your feeder conductors to each pedestal. The EGC will bond all of the non-current carrying metal parts back to source of electricity, the electrical service. Some people will argue that extra ground rods are good for lightning protection, but that's not how grounding works. The earth is not an effective fault return path, but your EGC is. If lightning stuck a pedestal with rods attached, the energy will dissipate through the earth. As the potential dissipates, it spreads out from the location of the ground strike. As soon as this energy comes across other pedestals with ground rods, there will be a difference of potential between the pedestals and ground rods and the current will now be induced onto the equipment grounding conductor and will pass through every piece of equipment connected to the system.
I have seen this many times with nonseparately derived system generators where installers connect an unnecessary ground rod to the generator frame because UL requires a terminal for such a connection. They see the terminal and assume it's required. The transfer equipment, not the generator determine if grounding electrodes are required. As soon as there is a lightning storm, the controller in the generator gets hit with a power surge and shorts out along with all of the electronics connected to the system. Unfortunately, this also happens where there are multiple building on structures connected to a common electrical service and requires the installation of multiple surge protective devices.
Hey Mike thanks for your question. There were some changes in the 2017 NEC that were intended to clear up some confusion. Grounding electrodes are not required for power outlets or recreational vehicle site supply equipment unless they are used as service equipment as stated in 551.75(B). The words "other than equipment" were added to the definition of Structure in Article 100 to help in this effort also.
I expect that not everyone will agree with you about auxiliary grounding electrodes, as allowed by 250.54, not serving a real purpose.
ABOUT CQD: NECA’s Code Question of the Day (CQD) is a leading National Electrical Code® forum for NECA and the industry. The CQD generates a lively dialogue and relative practical and Code-based responses to an ever-increasing and interactive audience.
IMPORTANT NOTICE: All answers are based on the latest edition of the National Electrical Code®, unless the question requests a response based on a specific edition. This correspondence is not a formal interpretation of the NEC®. Any responses expressed to the questions are opinions and do not necessarily represent the official position of NECA, NFPA, or any technical committee. In addition, this correspondence is neither intended, nor should it be relied upon, to provide professional consultation or services.
ABOUT CHARLIE: Charles M. Trout, better known as Charlie, was a nationally known NEC® expert and author. He served on several NEC® technical committees and is past chairman of CMP-12. In 2006 Charlie was awarded the prestigious Coggeshall Award for outstanding contributions to the electrical contracting industry, codes and standards development, and technical training. Charlie was also a member of NECA’s Academy of Electrical Contracting. Charlie’s experienced team of industry experts keep the CQD dialogue and discussions active and informative in the spirit of the man himself, as he wanted.
NECA STANDARDS: NECA publishes the National Electrical Installation Standards™ (NEIS™), a series of ANSI-approved performance and quality standards for electrical construction. Visit NECA-NEIS.org for more information. NEISÃ” can be purchased in three formats: as paper books, on CD, or as electronic downloads.
NECA SAFETY PRODUCTS: NECA publishes valuable electrical safety books and CDs for the industry. Visit necanet.org/store to view or purchase NECA safety products.
CONTACT US: To submit a Code question, subscribe, or unsubscribe from this list, please e-mail: email@example.com.
© 1999 – 2014 National Electrical Installation Standards. All rights reserved.
Brought to you by NECA. NECA is the voice of the electrical contracting industry NATIONAL ELECTRICAL INSTALLATION STANDARDS, NEIS and the NEIS logo are registered trademarks of the National Electrical Contractors Association.
Created by Matrix Group International, Inc.