Standards as High as Your Own
NECA Online Help Desk Please leave a message
Re: CQD answer published Wednesday, January 23, 2019 - Concrete Hole Raceway
Regarding the CQD for 1/23/2019 about the concrete wall hole-raceway:
My guess is that David's pronoun reference for "doing this a long time" meant that he had been doing electrical work a long time, not using holes in concrete as raceways. =}) Those darn pronouns can be pretty slippery.
In any case, this would have to be an installation which an inspector used their 90.4 authority to accept as safe. It certainly could be, as long as an equipment grounding conductor properly bonds the metals on both sides as required in Article 250. The concrete hole could be acceptable as a raceway under 90.4 since it is fully non-combustible. I have indeed received just such an approval (ahead of construction of course) for a case of an old exterior service being refed by a new exterior service - the multi-hundred amp feeder (1200 as I remember it) was run in just this manner.
The undisussed concern I would have is if one side of the wall of David's subject is exterior : How is the installation protected from water intrusion and corrosive damage?
Hey Scott thanks for your comment. As you and several others pointed out, he meant that he had been doing electrical work for a long time and "they" had installed the conductors through a concrete hole. We are sorry for inferring that he was doing that type of installation.
Getting the AHJ's thoughts on acceptance prior to doing an installation is a good idea. But allowing individual conductors to be installed through a hole in concrete doesn't seem to comply with 300.3(A) or 300.18(A) besides the concern about water and corrosion.
ABOUT CQD: NECA’s Code Question of the Day (CQD) is a leading National Electrical Code® forum for NECA and the industry. The CQD generates a lively dialogue and relative practical and Code-based responses to an ever-increasing and interactive audience.
IMPORTANT NOTICE: All answers are based on the latest edition of the National Electrical Code®, unless the question requests a response based on a specific edition. This correspondence is not a formal interpretation of the NEC®. Any responses expressed to the questions are opinions and do not necessarily represent the official position of NECA, NFPA, or any technical committee. In addition, this correspondence is neither intended, nor should it be relied upon, to provide professional consultation or services.
ABOUT CHARLIE: Charles M. Trout, better known as Charlie, was a nationally known NEC® expert and author. He served on several NEC® technical committees and is past chairman of CMP-12. In 2006 Charlie was awarded the prestigious Coggeshall Award for outstanding contributions to the electrical contracting industry, codes and standards development, and technical training. Charlie was also a member of NECA’s Academy of Electrical Contracting. Charlie’s experienced team of industry experts keep the CQD dialogue and discussions active and informative in the spirit of the man himself, as he wanted.
NECA STANDARDS: NECA publishes the National Electrical Installation Standards™ (NEIS™), a series of ANSI-approved performance and quality standards for electrical construction. Visit NECA-NEIS.org for more information. NEISÃ” can be purchased in three formats: as paper books, on CD, or as electronic downloads.
NECA SAFETY PRODUCTS: NECA publishes valuable electrical safety books and CDs for the industry. Visit necanet.org/store to view or purchase NECA safety products.
CONTACT US: To submit a Code question, subscribe, or unsubscribe from this list, please e-mail: firstname.lastname@example.org.
© 1999 – 2014 National Electrical Installation Standards. All rights reserved.
Brought to you by NECA. NECA is the voice of the electrical contracting industry NATIONAL ELECTRICAL INSTALLATION STANDARDS, NEIS and the NEIS logo are registered trademarks of the National Electrical Contractors Association.
Created by Matrix Group International, Inc.