Standards as High as Your Own
NECA Online Help Desk Please leave a message
Re: CQD answer published Wednesday, September 14, 2018 -Suspended Ceiling Luminaires 2
Good morning, I enjoy the Forum and all that you do. I am not sure if in today's answer you misspoke or perhaps we have a different interpretation of 410.36(B). As I understand it, the section covers ceiling systems used to support luminaires. If the luminaire is supported independently, such as by wires on opposite corners, it is supported by the wires and not by the ceiling system. As such, it is not required to secure the luminaire to the framing member. In this case, in the event a fire fighter removes all or a portion of the ceiling grid in the course of fighting a fire, the luminaires would remain in place if unattached to the grid. If attached, removing the grid would also bring down the luminaires. Seismic concerns are also covered by this logic. On the other hand, if the luminaire is supported solely by the grid, it must be secured to the grid per 410.36(B).
J Grant Hammett
Hey J Grant thanks for your comment and we are glad you enjoy CQD. Proposal 18-32 was Accepted in Principle during the processing of the 1987 NEC and the words "so supported" were removed from the second sentence of 410-16(c). The Panel Comment was " The Panel agrees that all Fixtures within a ceiling system should be attached to that ceiling system."
Comment 18-23 suggested adding an exception to not require fastening to a suspended ceiling where the "fixtures" are supported directly to the structural ceiling. That comment was rejected with the supporting wording: "It is the Panel's intent to require fixtures otherwise supported to be fastened to the grid."
It is understandable how your interpretation can be made with the existing wording. Consider submitting a Public Input for the 2023 NEC in 410.36(B) to improve the wording so it is clear the rule applies whether or not the suspended ceiling is the only means of support or not.
See tomorrows answer for even more information about luminaires in suspended ceilings.
ABOUT CQD: NECA’s Code Question of the Day (CQD) is a leading National Electrical Code® forum for NECA and the industry. The CQD generates a lively dialogue and relative practical and Code-based responses to an ever-increasing and interactive audience.
IMPORTANT NOTICE: All answers are based on the latest edition of the National Electrical Code®, unless the question requests a response based on a specific edition. This correspondence is not a formal interpretation of the NEC®. Any responses expressed to the questions are opinions and do not necessarily represent the official position of NECA, NFPA, or any technical committee. In addition, this correspondence is neither intended, nor should it be relied upon, to provide professional consultation or services.
ABOUT CHARLIE: Charles M. Trout, better known as Charlie, was a nationally known NEC® expert and author. He served on several NEC® technical committees and is past chairman of CMP-12. In 2006 Charlie was awarded the prestigious Coggeshall Award for outstanding contributions to the electrical contracting industry, codes and standards development, and technical training. Charlie was also a member of NECA’s Academy of Electrical Contracting. Charlie’s experienced team of industry experts keep the CQD dialogue and discussions active and informative in the spirit of the man himself, as he wanted.
NECA STANDARDS: NECA publishes the National Electrical Installation Standards™ (NEIS™), a series of ANSI-approved performance and quality standards for electrical construction. Visit NECA-NEIS.org for more information. NEISÃ” can be purchased in three formats: as paper books, on CD, or as electronic downloads.
NECA SAFETY PRODUCTS: NECA publishes valuable electrical safety books and CDs for the industry. Visit necanet.org/store to view or purchase NECA safety products.
CONTACT US: To submit a Code question, subscribe, or unsubscribe from this list, please e-mail: firstname.lastname@example.org.
© 1999 – 2014 National Electrical Installation Standards. All rights reserved.
Brought to you by NECA. NECA is the voice of the electrical contracting industry NATIONAL ELECTRICAL INSTALLATION STANDARDS, NEIS and the NEIS logo are registered trademarks of the National Electrical Contractors Association.
Created by Matrix Group International, Inc.