Standards as High as Your Own
NECA Online Help Desk Please leave a message
Charlie, Thank you for your service...enjoyable and very informative. Section 300.3(B) discusses conductors of the same circuit and in general, requires that all conductors (including the grounded conductor and all equipment grounding conductors and bonding conductors) to be contained within the same raceway, auxiliary gutter, cable tray, cablebus assembly, trench, cable, or cord unless otherwise permitted in accordance with 300.3(B)(1) through (B)(4). An exception under 300.3(B)(1) - Parallel Installations - allows conductors that are installed in underground, non-metallic raceways to be arranged as isolated phase installations as long as the raceways are installed in close proximity and comply with 300.20(B). Section 300.5(I) discusses conductors of the same circuit in underground installations. This section also requires all conductors of the same circuit (including the grounded conductor and all equipment grounding conductors) to be installed in the same raceway or cable "or shall be in close proximity in the same trench." Exception No. 2 under this section, however, allows isolated phase, polarity, grounded conductor, and equipment grounding and bonding conductor installations in non-metallic raceways in close proximity where conductors are paralleled as permitted in 310.10(H), and where the conditions of 300.20(B) are met.
Now to my question: For an underground 3 phase, 5 wire installation (3 phase conductors, an equipment grounding conductor, and a grounded conductor), can the 3 phase wires and the equipment grounding conductor be installed together in a single underground PVC conduit and the grounded conductor be installed in a separate, adjacent underground PVC conduit? The conductors are "installed in close proximity in the same trench" per the last sentence of Section 300.5(I) and this also appears to meet the general intent covered by Exception No. 2 under Section 300.5(I). However, this is not a parallel installation and each phase is not isolated. All phase conductors (and the equipment grounding conductor) are grouped together in one underground PVC conduit and the grounded conductor (the neutral) is installed in a separate underground PVC conduit with both conduits being side by side (i.e. in close proximity in the same trench). Thanks, Chris DeWeese
Hey Chris thanks for your question and the compliment. No, as you indicated the general rule in 300.3(B) is for all conductors of the same circuit, including grounded and equipment grounding conductors, to be in the same raceway, cable, etc. The exception to 300.3(B)(1) is for paralleled installations. The same concept is in Exception 2 to 300.5(I) for underground installations and is limited to parallel installations.
ABOUT CQD: NECA’s Code Question of the Day (CQD) is a leading National Electrical Code® forum for NECA and the industry. The CQD generates a lively dialogue and relative practical and Code-based responses to an ever-increasing and interactive audience.
IMPORTANT NOTICE: All answers are based on the latest edition of the National Electrical Code®, unless the question requests a response based on a specific edition. This correspondence is not a formal interpretation of the NEC®. Any responses expressed to the questions are opinions and do not necessarily represent the official position of NECA, NFPA, or any technical committee. In addition, this correspondence is neither intended, nor should it be relied upon, to provide professional consultation or services.
ABOUT CHARLIE: Charles M. Trout, better known as Charlie, was a nationally known NEC® expert and author. He served on several NEC® technical committees and is past chairman of CMP-12. In 2006 Charlie was awarded the prestigious Coggeshall Award for outstanding contributions to the electrical contracting industry, codes and standards development, and technical training. Charlie was also a member of NECA’s Academy of Electrical Contracting. Charlie’s experienced team of industry experts keep the CQD dialogue and discussions active and informative in the spirit of the man himself, as he wanted.
NECA STANDARDS: NECA publishes the National Electrical Installation Standards™ (NEIS™), a series of ANSI-approved performance and quality standards for electrical construction. Visit NECA-NEIS.org for more information. NEISÃ” can be purchased in three formats: as paper books, on CD, or as electronic downloads.
NECA SAFETY PRODUCTS: NECA publishes valuable electrical safety books and CDs for the industry. Visit necanet.org/store to view or purchase NECA safety products.
CONTACT US: To submit a Code question, subscribe, or unsubscribe from this list, please e-mail: firstname.lastname@example.org.
© 1999 – 2014 National Electrical Installation Standards. All rights reserved.
Brought to you by NECA. NECA is the voice of the electrical contracting industry NATIONAL ELECTRICAL INSTALLATION STANDARDS, NEIS and the NEIS logo are registered trademarks of the National Electrical Contractors Association.
Created by Matrix Group International, Inc.