Standards as High as Your Own
NECA Online Help Desk Please leave a message
A metal cabinet contains service conductors, their splices, and current transformers (CT), and is located upstream of an 800-amp service disconnecting means. The CT cabinet has only PVC raceways entering and exiting the enclosure, and the engineered drawings do not show any supply-side bonding jumpers in the PVC raceways. Is it correct to assume that this metal CT enclosure must be connected to a supply-side bonding jumper? If so, what is the correct size bonding jumper? Should supply-side bonding jumpers have been included in the drawings?
Although NEC Table 250.102 (C)(1) provides sizes of supply-side bonding jumpers, there seems to be no specific text section that references this table for metal enclosures. I have looked at 250.80, 250.92, and 250.102 (C). Can you help me connect the NEC dots to size supply-side bonding jumpers to metal CT enclosures?
Hey Curtis thanks for your question, you have the correct references. All metal enclosures (the CT cabinet) containing service conductors must be bonded as stated in 250.92(A)(2). The grounded conductor can be used to accomplish the required bonding as stated in 250.92(B)(1). In that case a supply side bonding jumper is not needed. If that is not done a Supply Side Bonding Jumper can be used as that term is defined in 250.2. The size is based on 250.102(C)(1) for a single raceway or 250.102(C)(2) for parallel raceways.
ABOUT CQD: NECA’s Code Question of the Day (CQD) is a leading National Electrical Code® forum for NECA and the industry. The CQD generates a lively dialogue and relative practical and Code-based responses to an ever-increasing and interactive audience.
IMPORTANT NOTICE: All answers are based on the latest edition of the National Electrical Code®, unless the question requests a response based on a specific edition. This correspondence is not a formal interpretation of the NEC®. Any responses expressed to the questions are opinions and do not necessarily represent the official position of NECA, NFPA, or any technical committee. In addition, this correspondence is neither intended, nor should it be relied upon, to provide professional consultation or services.
ABOUT CHARLIE: Charles M. Trout, better known as Charlie, was a nationally known NEC® expert and author. He served on several NEC® technical committees and is past chairman of CMP-12. In 2006 Charlie was awarded the prestigious Coggeshall Award for outstanding contributions to the electrical contracting industry, codes and standards development, and technical training. Charlie was also a member of NECA’s Academy of Electrical Contracting. Charlie’s experienced team of industry experts keep the CQD dialogue and discussions active and informative in the spirit of the man himself, as he wanted.
NECA STANDARDS: NECA publishes the National Electrical Installation Standards™ (NEIS™), a series of ANSI-approved performance and quality standards for electrical construction. Visit NECA-NEIS.org for more information. NEISÃ” can be purchased in three formats: as paper books, on CD, or as electronic downloads.
NECA SAFETY PRODUCTS: NECA publishes valuable electrical safety books and CDs for the industry. Visit necanet.org/store to view or purchase NECA safety products.
CONTACT US: To submit a Code question, subscribe, or unsubscribe from this list, please e-mail: email@example.com.
© 1999 – 2014 National Electrical Installation Standards. All rights reserved.
Brought to you by NECA. NECA is the voice of the electrical contracting industry NATIONAL ELECTRICAL INSTALLATION STANDARDS, NEIS and the NEIS logo are registered trademarks of the National Electrical Contractors Association.
Created by Matrix Group International, Inc.