Standards as High as Your Own
NECA Online Help Desk Please leave a message
Thank you for your code insight. I am confused, (my normal state) about 250.66 requirements for grounding electrode conductor size and 250.104 for water pipe and structural steel bonding. A service fed with 5 runs of 500 KCMIL copper would require a 3/0 grounding electrode conductor to the water pipe and building steel. However, 250.104 requires a 350 KCMIL copper the water pipe and building steel.
Am I confused, missing something, or merely misinformed.
Hey Mike thanks for your question and the kind words. No, you didn't miss anything, actually you point out an unintended rule.
The references in 250.104 were changed from Table 250.66 to Table 250.102(C)(1), in several places, for the 2017 NEC because the conductor is a bonding conductor, not a grounding electrode conductor. The largest grounding electrode conductor required by Table 250.66 is a 3/0 copper or 250 kcmil aluminum but bonding conductors and jumpers do not have the same limitation. This issue has been noted, and will hopefully be corrected for the 2020 NEC, to re-establish the 3/0 copper or 250 kcmil aluminum as maximum required sizes while retaining the correct terminology.
ABOUT CQD: The Code Question of the Day (CQD) is NECA and ELECTRICAL CONTRACTOR Magazine’s flagship National Electrical Code (NEC®) public forum for the industry, sponsored by EATON. The daily distribution of Q&A generates a lively dialogue and shares relative Code-based practical responses.
SUBMIT YOUR CODE QUESTION: Click here to submit a question to for inclusion in an upcoming edition of the Code Question of the Day, or email firstname.lastname@example.org.
CHARLIE TROUT: Charles M. Trout, better known as Charlie, was a nationally recognized NEC® expert and author. He served on several NEC technical committees and is past chairman of CMP-12. In 2006, Charlie was awarded NECA’s prestigious Coggeshall Award for outstanding contributions to the electrical contracting industry, codes and standards development and technical training. NECA continues to provide this public forum in memory and recognition of all his fine contributions that has made the NEC what it is today.
NECA STANDARDS: NECA publishes the National Electrical Installation Standards™ (NEIS™), a series of ANSI-approved performance and quality standards for electrical construction. NEIS can be purchased in the NECA Store in three formats: a printed or PDF download of a standard or, as an annual subscription service.
NECA SAFETY PRODUCTS & PUBLICATIONS: NECA produces electrical safety publications and products for the industry including jobsite safety guides, handbooks and resource kits. View a full listing of available resources and products »
IMPORTANT NOTICE: Unless the question requests a response based on a specific edition, all answers are based on the latest edition of NFPA 70® National Electrical Code®.
This correspondence is not a formal interpretation of the NEC® and any responses expressed to the questions are opinions and do not necessarily represent the official position of NECA, NFPA, the NEC Correlating Committee any Code-making panel or other electrical technical committee. In addition, this correspondence is neither intended, nor should it be relied upon, to provide professional consultation or services.
UPDATE YOUR SUBSCRIPTION PREFERENCES: Subscribe or Unsubscribe from this list.
© 1999 – 2014 National Electrical Installation Standards. All rights reserved.
Brought to you by NECA. NECA is the voice of the electrical contracting industry NATIONAL ELECTRICAL INSTALLATION STANDARDS, NEIS and the NEIS logo are registered trademarks of the National Electrical Contractors Association.
Created by Matrix Group International, Inc.