Standards as High as Your Own
NECA Online Help Desk Please leave a message
Thank you for your code insight. I am confused, (my normal state) about 250.66 requirements for grounding electrode conductor size and 250.104 for water pipe and structural steel bonding. A service fed with 5 runs of 500 KCMIL copper would require a 3/0 grounding electrode conductor to the water pipe and building steel. However, 250.104 requires a 350 KCMIL copper the water pipe and building steel.
Am I confused, missing something, or merely misinformed.
Hey Mike thanks for your question and the kind words. No, you didn't miss anything, actually you point out an unintended rule.
The references in 250.104 were changed from Table 250.66 to Table 250.102(C)(1), in several places, for the 2017 NEC because the conductor is a bonding conductor, not a grounding electrode conductor. The largest grounding electrode conductor required by Table 250.66 is a 3/0 copper or 250 kcmil aluminum but bonding conductors and jumpers do not have the same limitation. This issue has been noted, and will hopefully be corrected for the 2020 NEC, to re-establish the 3/0 copper or 250 kcmil aluminum as maximum required sizes while retaining the correct terminology.
ABOUT CQD: NECA’s Code Question of the Day (CQD) is a leading National Electrical Code® forum for NECA and the industry. The CQD generates a lively dialogue and relative practical and Code-based responses to an ever-increasing and interactive audience.
IMPORTANT NOTICE: All answers are based on the latest edition of the National Electrical Code®, unless the question requests a response based on a specific edition. This correspondence is not a formal interpretation of the NEC®. Any responses expressed to the questions are opinions and do not necessarily represent the official position of NECA, NFPA, or any technical committee. In addition, this correspondence is neither intended, nor should it be relied upon, to provide professional consultation or services.
ABOUT CHARLIE: Charles M. Trout, better known as Charlie, was a nationally known NEC® expert and author. He served on several NEC® technical committees and is past chairman of CMP-12. In 2006 Charlie was awarded the prestigious Coggeshall Award for outstanding contributions to the electrical contracting industry, codes and standards development, and technical training. Charlie was also a member of NECA’s Academy of Electrical Contracting. Charlie’s experienced team of industry experts keep the CQD dialogue and discussions active and informative in the spirit of the man himself, as he wanted.
NECA STANDARDS: NECA publishes the National Electrical Installation Standards™ (NEIS™), a series of ANSI-approved performance and quality standards for electrical construction. Visit NECA-NEIS.org for more information. NEISÃ” can be purchased in three formats: as paper books, on CD, or as electronic downloads.
NECA SAFETY PRODUCTS: NECA publishes valuable electrical safety books and CDs for the industry. Visit necanet.org/store to view or purchase NECA safety products.
CONTACT US: To submit a Code question, subscribe, or unsubscribe from this list, please e-mail: firstname.lastname@example.org.
© 1999 – 2014 National Electrical Installation Standards. All rights reserved.
Brought to you by NECA. NECA is the voice of the electrical contracting industry NATIONAL ELECTRICAL INSTALLATION STANDARDS, NEIS and the NEIS logo are registered trademarks of the National Electrical Contractors Association.
Created by Matrix Group International, Inc.