Standards as High as Your Own
NECA Online Help Desk Please leave a message
Can I run a class 2 circuit cable (outer sheath around insulated conductors) in same conduit as power based on 725.136(I)(2)?
Hey Zach thanks for your question. As you know Class 2 circuit cables and conductors cannot be in the same raceway with power conductors as stated in 725.136(A) - unless allowed by 725.136(B) through 725.136(I). A 2 inch separation is required between Class 2 conductors and power conductors as stated in 725.136(I) - unless allowed by (1) or (2). The 2 inch distance is removed if the Class 2 conductors are permanently separated from the power conductors by a continuous firmly fixed nonconductor such as porcelain tubes or flexible tubing in addition to the conductor insulation itself. Notice that the wording in (2) is between conductors, not between cables. So, if the AHJ considers the cable sheath to be a "firmly fixed nonconductor" they can allow the installation you are describing. Make sure you check with them before not after you do this.
ABOUT CQD: NECA’s Code Question of the Day (CQD) is a leading National Electrical Code® forum for NECA and the industry. The CQD generates a lively dialogue and relative practical and Code-based responses to an ever-increasing and interactive audience.
IMPORTANT NOTICE: All answers are based on the latest edition of the National Electrical Code®, unless the question requests a response based on a specific edition. This correspondence is not a formal interpretation of the NEC®. Any responses expressed to the questions are opinions and do not necessarily represent the official position of NECA, NFPA, or any technical committee. In addition, this correspondence is neither intended, nor should it be relied upon, to provide professional consultation or services.
ABOUT CHARLIE: Charles M. Trout, better known as Charlie, was a nationally known NEC® expert and author. He served on several NEC® technical committees and is past chairman of CMP-12. In 2006 Charlie was awarded the prestigious Coggeshall Award for outstanding contributions to the electrical contracting industry, codes and standards development, and technical training. Charlie was also a member of NECA’s Academy of Electrical Contracting. Charlie’s experienced team of industry experts keep the CQD dialogue and discussions active and informative in the spirit of the man himself, as he wanted.
NECA STANDARDS: NECA publishes the National Electrical Installation Standards™ (NEIS™), a series of ANSI-approved performance and quality standards for electrical construction. Visit NECA-NEIS.org for more information. NEISÃ” can be purchased in three formats: as paper books, on CD, or as electronic downloads.
NECA SAFETY PRODUCTS: NECA publishes valuable electrical safety books and CDs for the industry. Visit necanet.org/store to view or purchase NECA safety products.
CONTACT US: To submit a Code question, subscribe, or unsubscribe from this list, please e-mail: email@example.com.
© 1999 – 2014 National Electrical Installation Standards. All rights reserved.
Brought to you by NECA. NECA is the voice of the electrical contracting industry NATIONAL ELECTRICAL INSTALLATION STANDARDS, NEIS and the NEIS logo are registered trademarks of the National Electrical Contractors Association.
Created by Matrix Group International, Inc.