Standards as High as Your Own
NECA Online Help Desk Please leave a message
Gentlemen, I’m hoping you can help with an opinion.
As you seem to understand how to apply the NEC rules from a practical viewpoint. Section 230.72 indicates the two to six service disconnects permitted in Section 230.71 must be grouped. There is no maximum distance on between the two to six disconnects, so how far is too far before the installation would not meet the grouping requirement. Could signage be installed to assist in meeting the grouping requirement? Any opinions would be very appreciated.
Hi Mark, Thanks for the kind words and for your question.
Ah the old grouping issue… This one definitely gets into a gray area of the NEC that requires good practical and logical judgment by the AHJ. It also requires good communication and coordination with the installer. Here is our opinion. First, the reason for grouping is to help readily facilitate the disconnection of all power to the building or structure served. That said, the farther the distance between the service disconnects of a grouped arrangement to meet 230.72, the more the gray area is exasperated. The grouping requirement is easily achieved for all service disconnects that are installed side by side. In larger facilities, it is not uncommon to see multiple section service switchboards or switchgear (each with a service disconnect) to be installed in the same electric room of the building. Service disconnects in multiple large pieces of equipment in the same electric room are often considered by the AHJ to meet the grouping rule. Each six-disconnect installation warrants its own assessment to determine compliance. An example of noncompliance would be two of the six service disconnects installed on one corner of a building and the other four of the six installed on another corner or the same building. The Code does not include a maximum distance or any insight from (as defined) text that could assist when this judgement has to be applied. It is also worth noting that these sections 230.71 and 230.72 do not include any service disconnecting means identification and directory information as provided in Section 230.2(E). Perhaps this an opportunity for a proposed revision for the 2023 NEC which is now open for Public Input, visit www.nfpa.org.
ABOUT CQD: The Code Question of the Day (CQD) is NECA and ELECTRICAL CONTRACTOR Magazine’s flagship National Electrical Code (NEC®) public forum for the industry, sponsored by EATON. The daily distribution of Q&A generates a lively dialogue and shares relative Code-based practical responses.
SUBMIT YOUR CODE QUESTION: Click here to submit a question to for inclusion in an upcoming edition of the Code Question of the Day, or email email@example.com.
CHARLIE TROUT: Charles M. Trout, better known as Charlie, was a nationally known NEC® expert and author. He served on several NEC® technical committees and is past chairman of CMP-12. In 2006 Charlie was awarded the prestigious Coggeshall Award for outstanding contributions to the electrical contracting industry, codes and standards development, and technical training. Even though Charlie passed away in October of 2015, his work continues in spirit. NECA continues to maintain this question forum for its many subscribers in memory and recognition of all his significant contributions to making the NEC what it is today.
NECA STANDARDS: NECA publishes the National Electrical Installation Standards™ (NEIS™), a series of ANSI-approved performance and quality standards for electrical construction. NEIS can be purchased in the NECA Store in three formats: a printed or PDF download of a standard or, as an annual subscription service.
NECA SAFETY PRODUCTS & PUBLICATIONS: NECA produces electrical safety publications and products for the industry including jobsite safety guides, handbooks and resource kits. View a full listing of available resources and products »
IMPORTANT NOTICE: Unless the question requests a response based on a specific edition, all answers are based on the latest edition of NFPA 70® National Electrical Code®.
This correspondence is not a formal interpretation of the NEC® and any responses expressed to the questions are opinions and do not necessarily represent the official position of NECA, NFPA, the NEC Correlating Committee any Code-making panel or other electrical technical committee. In addition, this correspondence is neither intended, nor should it be relied upon, to provide professional consultation or services.
UPDATE YOUR SUBSCRIPTION PREFERENCES: Subscribe or Unsubscribe from this list.
© 1999 – 2014 National Electrical Installation Standards. All rights reserved.
Brought to you by NECA. NECA is the voice of the electrical contracting industry NATIONAL ELECTRICAL INSTALLATION STANDARDS, NEIS and the NEIS logo are registered trademarks of the National Electrical Contractors Association.
Created by Matrix Group International, Inc.