Standards as High as Your Own
NECA Online Help Desk Please leave a message
I recently attended an Arc Flash training class and the instructor spent a lot of time giving his personal opinion rather than delivering information. The issue of fuse reducers came up and he said they were illegal since the 2006 code or some such nonsense... he never could tell me why and got really agitated when I asked for more information. I have looked them up on the manufacturers site and they are UL listed and I cant find anything in the code telling me they have been banned. Do you have any information?
Hey Travis thanks for your question. There are some electrical trainers that maybe shouldn't be, just as there are many who do, or try to do, electrical work that are not qualified. There is a 2005 NEC and a 2008 NEC but no 2006 so maybe they are referring to a different code, a company or design specification, or maybe they heard it from someone who heard it from someone who made it up.
Fuse reducers are not prohibited by the NEC nor are they specifically addressed. The guide information for Fittings for Fuseholders, IZZR at productspec.ul.com indicates that "Consideration should be given to spacings when fuseholders are used within enclosures." Listed fuse reducers are available and as always the manufacturers instructions must be followed as stated in 110.3(B). If any fuse manufacturer or testing laboratory representative has more information please send it in and we will publish it.
See the following for more information:
ABOUT CQD: NECA’s Code Question of the Day (CQD) is a leading National Electrical Code® forum for NECA and the industry. The CQD generates a lively dialogue and relative practical and Code-based responses to an ever-increasing and interactive audience.
IMPORTANT NOTICE: All answers are based on the latest edition of the National Electrical Code®, unless the question requests a response based on a specific edition. This correspondence is not a formal interpretation of the NEC®. Any responses expressed to the questions are opinions and do not necessarily represent the official position of NECA, NFPA, or any technical committee. In addition, this correspondence is neither intended, nor should it be relied upon, to provide professional consultation or services.
ABOUT CHARLIE: Charles M. Trout, better known as Charlie, was a nationally known NEC® expert and author. He served on several NEC® technical committees and is past chairman of CMP-12. In 2006 Charlie was awarded the prestigious Coggeshall Award for outstanding contributions to the electrical contracting industry, codes and standards development, and technical training. Charlie was also a member of NECA’s Academy of Electrical Contracting. Charlie’s experienced team of industry experts keep the CQD dialogue and discussions active and informative in the spirit of the man himself, as he wanted.
NECA STANDARDS: NECA publishes the National Electrical Installation Standards™ (NEIS™), a series of ANSI-approved performance and quality standards for electrical construction. Visit NECA-NEIS.org for more information. NEISÃ” can be purchased in three formats: as paper books, on CD, or as electronic downloads.
NECA SAFETY PRODUCTS: NECA publishes valuable electrical safety books and CDs for the industry. Visit necanet.org/store to view or purchase NECA safety products.
CONTACT US: To submit a Code question, subscribe, or unsubscribe from this list, please e-mail: email@example.com.
© 1999 – 2014 National Electrical Installation Standards. All rights reserved.
Brought to you by NECA. NECA is the voice of the electrical contracting industry NATIONAL ELECTRICAL INSTALLATION STANDARDS, NEIS and the NEIS logo are registered trademarks of the National Electrical Contractors Association.
Created by Matrix Group International, Inc.