Standards as High as Your Own
NECA Online Help Desk Please leave a message
Re: CQD answer published Thursday, September 7, 2017 - Ground Rod Electrode Installation2
Charlie, keep up the good work on the CODE question of the day.
I am not sure if most installers are aware of the “chemical” ground rod options that are on the market today. Here is a link to our version but there are others that are UL467 listed as ground electrodes and can be installed in a vertical trench. http://www.thermoweld.com/docs/librariesprovider7/literature/flyers/ul-listed-chemical-ground-rod-flyer.pdf?sfvrsn=4
These rods were developed to deliver very low resistance to earth for sensitive installations where 5 ohms or less is required in any soil and to maintain that low resistance for the life of the installation. I am not sure what labor rate these installers may be using, but with the bending (not approved or recommended) and trenching (must be at least 28” or it is ineffective and unsafe) they are already doing, keeping some of the horizontal kit versions with them might be a cost savings in the long run and their clients will have an excellent ground resistance at the electrode. It is highly unlikely they are achieving 25 ohms or less with the other installation practices. Checking these electrodes annually as part of the ground system check up is recommended.
We do have other options for solid rock when no holes can be drilled but each one becomes more difficult to install and obtain low resistance to earth and the AHJ would have to sign off on those options as non Listed in most instances.
Director Specification Engineering
Hey Lee thanks for the additional information and kind words. Often grounds are used because they seem to be the least expensive option but you have a good point other types of grounding electrodes such as those stated in 250.52(A) can be used and could be a better alternative.
ABOUT CQD: NECA’s Code Question of the Day (CQD) is a leading National Electrical Code® forum for NECA and the industry. The CQD generates a lively dialogue and relative practical and Code-based responses to an ever-increasing and interactive audience.
IMPORTANT NOTICE: All answers are based on the latest edition of the National Electrical Code®, unless the question requests a response based on a specific edition. This correspondence is not a formal interpretation of the NEC®. Any responses expressed to the questions are opinions and do not necessarily represent the official position of NECA, NFPA, or any technical committee. In addition, this correspondence is neither intended, nor should it be relied upon, to provide professional consultation or services.
ABOUT CHARLIE: Charles M. Trout, better known as Charlie, was a nationally known NEC® expert and author. He served on several NEC® technical committees and is past chairman of CMP-12. In 2006 Charlie was awarded the prestigious Coggeshall Award for outstanding contributions to the electrical contracting industry, codes and standards development, and technical training. Charlie was also a member of NECA’s Academy of Electrical Contracting. Charlie’s experienced team of industry experts keep the CQD dialogue and discussions active and informative in the spirit of the man himself, as he wanted.
NECA STANDARDS: NECA publishes the National Electrical Installation Standards™ (NEIS™), a series of ANSI-approved performance and quality standards for electrical construction. Visit NECA-NEIS.org for more information. NEISÃ” can be purchased in three formats: as paper books, on CD, or as electronic downloads.
NECA SAFETY PRODUCTS: NECA publishes valuable electrical safety books and CDs for the industry. Visit necanet.org/store to view or purchase NECA safety products.
CONTACT US: To submit a Code question, subscribe, or unsubscribe from this list, please e-mail: firstname.lastname@example.org.
© 1999 – 2014 National Electrical Installation Standards. All rights reserved.
Brought to you by NECA. NECA is the voice of the electrical contracting industry NATIONAL ELECTRICAL INSTALLATION STANDARDS, NEIS and the NEIS logo are registered trademarks of the National Electrical Contractors Association.
Created by Matrix Group International, Inc.