Standards as High as Your Own
NECA Online Help Desk Please leave a message
Re: CQD answer published Thursday, August 31, 2017 -Dwelling Kitchen Receptacles
Wouldn’t the maximum number of receptacles be determined by the load? A duplex receptacle should be counted as 180VA minimum. If all receptacles are 20A duplex, then loading the circuit to 80% (16A) would yield a maximum of 10 receptacles. If you are allowed to load to 100%, then you could go to a maximum of 13.
In a Kitchen, we find we need more circuits than 2. We rarely feed more than two receptacles per circuit due to the fact that Kitchen appliances can be large heat loads and one appliance can be the entire load for a 20A circuit. ( i.e Coffee pots at 1200VA, refrigerator at 800VA, Electric skillet at 1500VA, Crock pot at 1200-1500VA, etc)
Hey Alex thanks for your follow up question. No, notice that wording in 220.14(J) specifically excludes receptacle outlets in dwelling occupancies from being calculated at 180 volt amperes. Receptacle outlets are generally required to be located to minimize the use of extension cords. If we installed more receptacle outlets than what is required, that would not likely increase the load as some would probably not be used. You can increase the number of receptacle outlets as you suggest, and that could be a better design, but is not specifically required.
ABOUT CQD: NECA’s Code Question of the Day (CQD) is a leading National Electrical Code® forum for NECA and the industry. The CQD generates a lively dialogue and relative practical and Code-based responses to an ever-increasing and interactive audience.
IMPORTANT NOTICE: All answers are based on the latest edition of the National Electrical Code®, unless the question requests a response based on a specific edition. This correspondence is not a formal interpretation of the NEC®. Any responses expressed to the questions are opinions and do not necessarily represent the official position of NECA, NFPA, or any technical committee. In addition, this correspondence is neither intended, nor should it be relied upon, to provide professional consultation or services.
ABOUT CHARLIE: Charles M. Trout, better known as Charlie, was a nationally known NEC® expert and author. He served on several NEC® technical committees and is past chairman of CMP-12. In 2006 Charlie was awarded the prestigious Coggeshall Award for outstanding contributions to the electrical contracting industry, codes and standards development, and technical training. Charlie was also a member of NECA’s Academy of Electrical Contracting. Charlie’s experienced team of industry experts keep the CQD dialogue and discussions active and informative in the spirit of the man himself, as he wanted.
NECA STANDARDS: NECA publishes the National Electrical Installation Standards™ (NEIS™), a series of ANSI-approved performance and quality standards for electrical construction. Visit NECA-NEIS.org for more information. NEISÃ” can be purchased in three formats: as paper books, on CD, or as electronic downloads.
NECA SAFETY PRODUCTS: NECA publishes valuable electrical safety books and CDs for the industry. Visit necanet.org/store to view or purchase NECA safety products.
CONTACT US: To submit a Code question, subscribe, or unsubscribe from this list, please e-mail: email@example.com.
© 1999 – 2014 National Electrical Installation Standards. All rights reserved.
Brought to you by NECA. NECA is the voice of the electrical contracting industry NATIONAL ELECTRICAL INSTALLATION STANDARDS, NEIS and the NEIS logo are registered trademarks of the National Electrical Contractors Association.
Created by Matrix Group International, Inc.