Standards as High as Your Own
NECA Online Help Desk Please leave a message
Can you use 12ga thhn stranded wire in EMT conduit coming from a 20 amp breaker that feeds a few outlets and flood lights (led)?
What are the spacing dimensions required to secure conduit?
I was getting bids to run another 220v circuit into the laundry room and was wondering why you couldn't run two 220v outlets from one breaker?
I'm not an electrician but I've come across a few questionable things licensed electricians have done so to make me feel better I like to understand the logic behind the installation.
Hey Justin thanks for your questions.
1) Yes 12 AWG copper stranded conductors can be protected by using a 20 ampere circuit breaker - if the conductor does not have "reduced" ampacity due to adjustment factors or correction factors as stated in 240.4 and 310.15. The conductor would also need to have sufficient ampacity for the load as stated in 210.19.
2) Support spacing distances vary based on the type of conduit, raceway or cable. See the XXX.30 section in the Article in NEC Chapter 3 for maximum spacing distances and the distances for securing at terminations.
3) Branch circuits can supply more than one receptacle outlet if the conductors are suitable for the load, properly protected from overcurrent, and meet any specific requirements depending on what they are installed for as stated in Article 210, 240.4, and 310.15.
ABOUT CQD: NECA’s Code Question of the Day (CQD) is a leading National Electrical Code® forum for NECA and the industry. The CQD generates a lively dialogue and relative practical and Code-based responses to an ever-increasing and interactive audience.
IMPORTANT NOTICE: All answers are based on the latest edition of the National Electrical Code®, unless the question requests a response based on a specific edition. This correspondence is not a formal interpretation of the NEC®. Any responses expressed to the questions are opinions and do not necessarily represent the official position of NECA, NFPA, or any technical committee. In addition, this correspondence is neither intended, nor should it be relied upon, to provide professional consultation or services.
ABOUT CHARLIE: Charles M. Trout, better known as Charlie, was a nationally known NEC® expert and author. He served on several NEC® technical committees and is past chairman of CMP-12. In 2006 Charlie was awarded the prestigious Coggeshall Award for outstanding contributions to the electrical contracting industry, codes and standards development, and technical training. Charlie was also a member of NECA’s Academy of Electrical Contracting. Charlie’s experienced team of industry experts keep the CQD dialogue and discussions active and informative in the spirit of the man himself, as he wanted.
NECA STANDARDS: NECA publishes the National Electrical Installation Standards™ (NEIS™), a series of ANSI-approved performance and quality standards for electrical construction. Visit NECA-NEIS.org for more information. NEISÃ” can be purchased in three formats: as paper books, on CD, or as electronic downloads.
NECA SAFETY PRODUCTS: NECA publishes valuable electrical safety books and CDs for the industry. Visit necanet.org/store to view or purchase NECA safety products.
CONTACT US: To submit a Code question, subscribe, or unsubscribe from this list, please e-mail: email@example.com.
© 1999 – 2014 National Electrical Installation Standards. All rights reserved.
Brought to you by NECA. NECA is the voice of the electrical contracting industry NATIONAL ELECTRICAL INSTALLATION STANDARDS, NEIS and the NEIS logo are registered trademarks of the National Electrical Contractors Association.
Created by Matrix Group International, Inc.