Standards as High as Your Own
NECA Online Help Desk Please leave a message
I have just bought an old house (ca 1965) to serve as my primary domicile. I bought it with the knowledge that the existing electrical installation isn't up to snuff. The specific issues I'd like to address are that there are no grounded outlets anywhere in the house, many fewer outlets and lights than needed, no GFI circuits, an aluminum input wire to the 100 amp breaker box (the rest of the house is 12 gauge, or better, copper) and no ground stake. The major work will be done by professionals but putting in the missing ground wires, locating and installing the extra outlets and switches along with the attendant new wiring is something I can do. And now, finally, the question I need to have answered is, "When upgrading the existing, ungrounded outlets, will single, naked copper ground wire, ran alongside the existing copper supply and correctly connected to each new, three prong outlet meet code?
Hey William thanks for your question. Yes, what you are suggesting can be done if it meets the rules in 250.130(C) and 406.4(D). A "separate" equipment grounding conductor can be run from the new grounding type receptacles (replacing the existing non-grounding type receptacles) but it must be connected to any of the items in 250.130(C). Most of those items are probably near or within the paneboard (breaker box) that supplies the outlets. The separate equipment grounding conductors must be protected from physical damage by being in an identified raceway or cable armor if smaller that 6 AWG.
ABOUT CQD: NECA’s Code Question of the Day (CQD) is a leading National Electrical Code® forum for NECA and the industry. The CQD generates a lively dialogue and relative practical and Code-based responses to an ever-increasing and interactive audience.
IMPORTANT NOTICE: All answers are based on the latest edition of the National Electrical Code®, unless the question requests a response based on a specific edition. This correspondence is not a formal interpretation of the NEC®. Any responses expressed to the questions are opinions and do not necessarily represent the official position of NECA, NFPA, or any technical committee. In addition, this correspondence is neither intended, nor should it be relied upon, to provide professional consultation or services.
ABOUT CHARLIE: Charles M. Trout, better known as Charlie, was a nationally known NEC® expert and author. He served on several NEC® technical committees and is past chairman of CMP-12. In 2006 Charlie was awarded the prestigious Coggeshall Award for outstanding contributions to the electrical contracting industry, codes and standards development, and technical training. Charlie was also a member of NECA’s Academy of Electrical Contracting. Charlie’s experienced team of industry experts keep the CQD dialogue and discussions active and informative in the spirit of the man himself, as he wanted.
NECA STANDARDS: NECA publishes the National Electrical Installation Standards™ (NEIS™), a series of ANSI-approved performance and quality standards for electrical construction. Visit NECA-NEIS.org for more information. NEISÃ” can be purchased in three formats: as paper books, on CD, or as electronic downloads.
NECA SAFETY PRODUCTS: NECA publishes valuable electrical safety books and CDs for the industry. Visit necanet.org/store to view or purchase NECA safety products.
CONTACT US: To submit a Code question, subscribe, or unsubscribe from this list, please e-mail: firstname.lastname@example.org.
© 1999 – 2014 National Electrical Installation Standards. All rights reserved.
Brought to you by NECA. NECA is the voice of the electrical contracting industry NATIONAL ELECTRICAL INSTALLATION STANDARDS, NEIS and the NEIS logo are registered trademarks of the National Electrical Contractors Association.
Created by Matrix Group International, Inc.