Standards as High as Your Own
NECA Online Help Desk Please leave a message
Hello and thanks for this forum,
My question is about sizing overcurrent protection for a 40HP 3 phase motor. I will be using a breaker. I do the following calculations: 40 hp motor- Table 430.250 full load current 52-amps. According to table 430.52 If I use an Inverse time breaker, I multiply that 52-amps by 250% which is 130-amps and according to the exceptions to non-standard sizes, I can go to the next up standard size. That would be a 150-amp breaker. I have two motor slide charts, one from Square D and one from Schneider and they both give different answers. The Square D slide table says a 40 HP three phase motor is to be protected by a 90-amp breaker and the Schneider slide chart states that a 40 hp is to be protected by a 100-amp breaker. What is the correct answer? How are my calculations wrong?
Thanks for participating and for your question. You didn't mention the voltage in this question but based on the ampere value provided from Table 430.250, it’s presumed at 460-480 volts. Your methodology is correct, but remember you are using the NEC to calculate what the maximum rating of the branch circuit, short circuit and ground fault protective device would be required not to exceed. The values provided in the slide charts are more conservative and specify breakers that will work to carry locked rotor currents during starting conditions and provide the necessary branch circuit short circuit, ground fault protection as well. Remember to address the overload protection as required in Part III of Article 430.
ABOUT CQD: The Code Question of the Day (CQD) is NECA and ELECTRICAL CONTRACTOR Magazine’s flagship National Electrical Code (NEC®) public forum for the industry, sponsored by EATON. The daily distribution of Q&A generates a lively dialogue and shares relative Code-based practical responses.
SUBMIT YOUR CODE QUESTION: Click here to submit a question to for inclusion in an upcoming edition of the Code Question of the Day, or email firstname.lastname@example.org.
CHARLIE TROUT: Charles M. Trout, better known as Charlie, was a nationally known NEC® expert and author. He served on several NEC® technical committees and is past chairman of CMP-12. In 2006 Charlie was awarded the prestigious Coggeshall Award for outstanding contributions to the electrical contracting industry, codes and standards development, and technical training. Even though Charlie passed away in October of 2015, his work continues in spirit. NECA continues to maintain this question forum for its many subscribers in memory and recognition of all his significant contributions to making the NEC what it is today.
NECA STANDARDS: NECA publishes the National Electrical Installation Standards™ (NEIS™), a series of ANSI-approved performance and quality standards for electrical construction. NEIS can be purchased in the NECA Store in three formats: a printed or PDF download of a standard or, as an annual subscription service.
NECA SAFETY PRODUCTS & PUBLICATIONS: NECA produces electrical safety publications and products for the industry including jobsite safety guides, handbooks and resource kits. View a full listing of available resources and products »
IMPORTANT NOTICE: Unless the question requests a response based on a specific edition, all answers are based on the latest edition of NFPA 70® National Electrical Code®.
This correspondence is not a formal interpretation of the NEC® and any responses expressed to the questions are opinions and do not necessarily represent the official position of NECA, NFPA, the NEC Correlating Committee any Code-making panel or other electrical technical committee. In addition, this correspondence is neither intended, nor should it be relied upon, to provide professional consultation or services.
UPDATE YOUR SUBSCRIPTION PREFERENCES: Subscribe or Unsubscribe from this list.
© 1999 – 2014 National Electrical Installation Standards. All rights reserved.
Brought to you by NECA. NECA is the voice of the electrical contracting industry NATIONAL ELECTRICAL INSTALLATION STANDARDS, NEIS and the NEIS logo are registered trademarks of the National Electrical Contractors Association.
Created by Matrix Group International, Inc.