Standards as High as Your Own
NECA Online Help Desk Please leave a message
Re: CQD answer published Friday, July 12, 2019 -480 V 3 wire needs 277 V-2
Sirs: As always, thank you for your valuable service. It is appreciated by many. Regarding 'converting' 3 phase 480 volt to lighting poles to 1 phase and deriving a neutral. Would it be legal and code-compliant to disconnect one phase at the breaker; re-identify it as a neutral; change the 3-pole breaker to a 2-pole single phase breaker; and obtain your neutral in that fashion?
With so many conversions of parking lot lights to LED, there is often as much as a 75% reduction in load and many of the lights are 277v instead of the old 480v. The old systems didn't need a neutral; with 277v lighting this would seem to be the easiest conversion.
Is it allowable? Thank you, Gary
Hey Gary thanks for your question and the kind words. Yes, if a neutral point, as defined in Article 100, exists on the transformer supplying the circuit and the neural conductor is grounded and if the grounded conductor is 4 AWG or larger and it is identified with white or gray marking at their terminations as stated in 200.6(B)(4). That might be a cost-effective solution.
ABOUT CQD: NECA’s Code Question of the Day (CQD) is a leading National Electrical Code® forum for NECA and the industry. The CQD generates a lively dialogue and relative practical and Code-based responses to an ever-increasing and interactive audience.
IMPORTANT NOTICE: All answers are based on the latest edition of the National Electrical Code®, unless the question requests a response based on a specific edition. This correspondence is not a formal interpretation of the NEC®. Any responses expressed to the questions are opinions and do not necessarily represent the official position of NECA, NFPA, or any technical committee. In addition, this correspondence is neither intended, nor should it be relied upon, to provide professional consultation or services.
ABOUT CHARLIE: Charles M. Trout, better known as Charlie, was a nationally known NEC® expert and author. He served on several NEC® technical committees and is past chairman of CMP-12. In 2006 Charlie was awarded the prestigious Coggeshall Award for outstanding contributions to the electrical contracting industry, codes and standards development, and technical training. Charlie was also a member of NECA’s Academy of Electrical Contracting. Charlie’s experienced team of industry experts keep the CQD dialogue and discussions active and informative in the spirit of the man himself, as he wanted.
NECA STANDARDS: NECA publishes the National Electrical Installation Standards™ (NEIS™), a series of ANSI-approved performance and quality standards for electrical construction. Visit NECA-NEIS.org for more information. NEISÃ” can be purchased in three formats: as paper books, on CD, or as electronic downloads.
NECA SAFETY PRODUCTS: NECA publishes valuable electrical safety books and CDs for the industry. Visit necanet.org/store to view or purchase NECA safety products.
CONTACT US: To submit a Code question, subscribe, or unsubscribe from this list, please e-mail: firstname.lastname@example.org.
© 1999 – 2014 National Electrical Installation Standards. All rights reserved.
Brought to you by NECA. NECA is the voice of the electrical contracting industry NATIONAL ELECTRICAL INSTALLATION STANDARDS, NEIS and the NEIS logo are registered trademarks of the National Electrical Contractors Association.
Created by Matrix Group International, Inc.