Standards as High as Your Own
NECA Online Help Desk Please leave a message
What is the length of run in a 2" PVC Conduit before it needs an expansion coupling?
Hey Glen thanks for your question. It depends on the amount of temperature change the PVC conduit will be exposed to. If the conduit length in a straight run changes 1/4 inch or more between securely mounted items, an expansion fitting is necessary as stated in 352.44. For example using a 65 degree F temperature change (such as for 30 to 95 degrees) in the center column of Table 352.44 gives us 2.64 inches of change in 100 feet or .264 in 10 ft which is a little more than 1/4 in (.25). Follow the manufacturer's instructions when setting the position of the expansion based on the temperature at the time of installation. For example, if the fitting is "bottomed out" while the temperature is not at the maximum the conduit will buckle or the items at the end will be damaged or move as the conduit expands when the temperature rises.
A free publication about expansion fittings is available from NEMA at:
ABOUT CQD: NECA’s Code Question of the Day (CQD) is a leading National Electrical Code® forum for NECA and the industry. The CQD generates a lively dialogue and relative practical and Code-based responses to an ever-increasing and interactive audience.
IMPORTANT NOTICE: All answers are based on the latest edition of the National Electrical Code®, unless the question requests a response based on a specific edition. This correspondence is not a formal interpretation of the NEC®. Any responses expressed to the questions are opinions and do not necessarily represent the official position of NECA, NFPA, or any technical committee. In addition, this correspondence is neither intended, nor should it be relied upon, to provide professional consultation or services.
ABOUT CHARLIE: Charles M. Trout, better known as Charlie, was a nationally known NEC® expert and author. He served on several NEC® technical committees and is past chairman of CMP-12. In 2006 Charlie was awarded the prestigious Coggeshall Award for outstanding contributions to the electrical contracting industry, codes and standards development, and technical training. Charlie was also a member of NECA’s Academy of Electrical Contracting. Charlie’s experienced team of industry experts keep the CQD dialogue and discussions active and informative in the spirit of the man himself, as he wanted.
NECA STANDARDS: NECA publishes the National Electrical Installation Standards™ (NEIS™), a series of ANSI-approved performance and quality standards for electrical construction. Visit NECA-NEIS.org for more information. NEISÃ” can be purchased in three formats: as paper books, on CD, or as electronic downloads.
NECA SAFETY PRODUCTS: NECA publishes valuable electrical safety books and CDs for the industry. Visit necanet.org/store to view or purchase NECA safety products.
CONTACT US: To submit a Code question, subscribe, or unsubscribe from this list, please e-mail: firstname.lastname@example.org.
© 1999 – 2014 National Electrical Installation Standards. All rights reserved.
Brought to you by NECA. NECA is the voice of the electrical contracting industry NATIONAL ELECTRICAL INSTALLATION STANDARDS, NEIS and the NEIS logo are registered trademarks of the National Electrical Contractors Association.
Created by Matrix Group International, Inc.