Standards as High as Your Own
NECA Online Help Desk Please leave a message
When doing a rewire in a dwelling of an existing AC or heating unit if there is no outlet within 25’ are you required to provide one
Hey David thanks for your question. Section 210.63 requires a 15 or 20 ampere 125 volt receptacle outlet be installed within 25 feet of heating, air-conditioning, and refrigeration equipment. That section does not have specific wording about what and when the receptacle outlet or the described equipment get installed.
For a new installation it is simple, if that type of utilization equipment is installed the receptacle outlet must also be installed. If you are only rewiring that type of existing utilization equipment then most AHJ's probably would not require a receptacle be installed. If you are rewiring that part of the dwelling then the AHJ might require a receptacle outlet be installed, the final decision is up to the AHJ. Maybe some AHJ's will send in comments with their thoughts. Even if not specifically required, providing a receptacle outlet will likely be useful in the future when servicing the equipment.
ABOUT CQD: NECA’s Code Question of the Day (CQD) is a leading National Electrical Code® forum for NECA and the industry. The CQD generates a lively dialogue and relative practical and Code-based responses to an ever-increasing and interactive audience.
IMPORTANT NOTICE: All answers are based on the latest edition of the National Electrical Code®, unless the question requests a response based on a specific edition. This correspondence is not a formal interpretation of the NEC®. Any responses expressed to the questions are opinions and do not necessarily represent the official position of NECA, NFPA, or any technical committee. In addition, this correspondence is neither intended, nor should it be relied upon, to provide professional consultation or services.
ABOUT CHARLIE: Charles M. Trout, better known as Charlie, was a nationally known NEC® expert and author. He served on several NEC® technical committees and is past chairman of CMP-12. In 2006 Charlie was awarded the prestigious Coggeshall Award for outstanding contributions to the electrical contracting industry, codes and standards development, and technical training. Charlie was also a member of NECA’s Academy of Electrical Contracting. Charlie’s experienced team of industry experts keep the CQD dialogue and discussions active and informative in the spirit of the man himself, as he wanted.
NECA STANDARDS: NECA publishes the National Electrical Installation Standards™ (NEIS™), a series of ANSI-approved performance and quality standards for electrical construction. Visit NECA-NEIS.org for more information. NEISÃ” can be purchased in three formats: as paper books, on CD, or as electronic downloads.
NECA SAFETY PRODUCTS: NECA publishes valuable electrical safety books and CDs for the industry. Visit necanet.org/store to view or purchase NECA safety products.
CONTACT US: To submit a Code question, subscribe, or unsubscribe from this list, please e-mail: email@example.com.
© 1999 – 2014 National Electrical Installation Standards. All rights reserved.
Brought to you by NECA. NECA is the voice of the electrical contracting industry NATIONAL ELECTRICAL INSTALLATION STANDARDS, NEIS and the NEIS logo are registered trademarks of the National Electrical Contractors Association.
Created by Matrix Group International, Inc.