Standards as High as Your Own
NECA Online Help Desk Please leave a message
Hello Charlie, long time reader here. My name is Steve, I'm a Vermont electrician with a question about meter enclosures I'm hoping you can help me with. It would appear there is a dispute in just what the 1/4" knockouts on the bottom of your meters are really for.
Some say it's for the GEC (Grounding Electrode conductor), usually a bare #6 or #4 copper wire to simply run through. Others claim a 'Kenny Clamp' or other sort of listed connector is to be used. What is to code?....are the NEC passage(s) below being applicable
Thank you for your time, Steve Vermont Electrician
Hey Steve thanks for your question. Holes can be provided in enclosures by manufacturers for a variety of purposes including drainage and ventilation. Knockouts are also often provided to be used for ease in installing connectors to enclosures but are not provided in all enclosures. The enclosure manufacturer should be able to tell you what theirs are intended to be used for. There is no specific requirement in the NEC to secure grounding electrode conductors (GEC) to enclosures or to provide a specific bushing or fitting. See 250.64(E)
ABOUT CQD: NECA’s Code Question of the Day (CQD) is a leading National Electrical Code® forum for NECA and the industry. The CQD generates a lively dialogue and relative practical and Code-based responses to an ever-increasing and interactive audience.
IMPORTANT NOTICE: All answers are based on the latest edition of the National Electrical Code®, unless the question requests a response based on a specific edition. This correspondence is not a formal interpretation of the NEC®. Any responses expressed to the questions are opinions and do not necessarily represent the official position of NECA, NFPA, or any technical committee. In addition, this correspondence is neither intended, nor should it be relied upon, to provide professional consultation or services.
ABOUT CHARLIE: Charles M. Trout, better known as Charlie, was a nationally known NEC® expert and author. He served on several NEC® technical committees and is past chairman of CMP-12. In 2006 Charlie was awarded the prestigious Coggeshall Award for outstanding contributions to the electrical contracting industry, codes and standards development, and technical training. Charlie was also a member of NECA’s Academy of Electrical Contracting. Charlie’s experienced team of industry experts keep the CQD dialogue and discussions active and informative in the spirit of the man himself, as he wanted.
NECA STANDARDS: NECA publishes the National Electrical Installation Standards™ (NEIS™), a series of ANSI-approved performance and quality standards for electrical construction. Visit NECA-NEIS.org for more information. NEISÃ” can be purchased in three formats: as paper books, on CD, or as electronic downloads.
NECA SAFETY PRODUCTS: NECA publishes valuable electrical safety books and CDs for the industry. Visit necanet.org/store to view or purchase NECA safety products.
CONTACT US: To submit a Code question, subscribe, or unsubscribe from this list, please e-mail: email@example.com.
© 1999 – 2014 National Electrical Installation Standards. All rights reserved.
Brought to you by NECA. NECA is the voice of the electrical contracting industry NATIONAL ELECTRICAL INSTALLATION STANDARDS, NEIS and the NEIS logo are registered trademarks of the National Electrical Contractors Association.
Created by Matrix Group International, Inc.