Standards as High as Your Own
NECA Online Help Desk Please leave a message
Greetings, I have a question regarding leaving live lamp sockets un-lamped. In my specific case, the luminaire has been a sconce containing 2 GU24 sockets for use with A19 lamps. The following link is not the exact sconce but has the same characteristics: open on top, closed/tight to wall on sides and bottom. It's mounted ~5.5' AFF in a hallway setting and the luminaire is wired with 120V power. The reason for leaving the second socket un-lamped is energy savings and sufficient illuminance from a single lamp. Can you tell me whether the NEC allows one of the sockets be left un-lamped? Can you tell me where in the NEC guidance might be provided? My specific applications are using the 2008 and 2011 versions of the NEC. Thanks for any help you can provide.
Hey Brennan thanks for your question. The NEC does not specifically address leaving a lampholder energized with out a lamp installed. Live parts must be guarded as stated in 110.27 and "lighting equipment" live parts cannot be normally exposed as stated in 410.5. It has been a common practice to remove some fluorescent lamps for energy conservation purposes while leaving the lampholders energized. There have been OSHA citations for open medium base lampholders (sockets) on construction sites but we are not aware of any for the application you are describing. It doesn't seem like a problem, especially within a partially enclosed luminaire, but that is not a guarantee that some inspector might not agree so ask the local AHJ for their thoughts.
ABOUT CQD: NECA’s Code Question of the Day (CQD) is a leading National Electrical Code® forum for NECA and the industry. The CQD generates a lively dialogue and relative practical and Code-based responses to an ever-increasing and interactive audience.
IMPORTANT NOTICE: All answers are based on the latest edition of the National Electrical Code®, unless the question requests a response based on a specific edition. This correspondence is not a formal interpretation of the NEC®. Any responses expressed to the questions are opinions and do not necessarily represent the official position of NECA, NFPA, or any technical committee. In addition, this correspondence is neither intended, nor should it be relied upon, to provide professional consultation or services.
ABOUT CHARLIE: Charles M. Trout, better known as Charlie, was a nationally known NEC® expert and author. He served on several NEC® technical committees and is past chairman of CMP-12. In 2006 Charlie was awarded the prestigious Coggeshall Award for outstanding contributions to the electrical contracting industry, codes and standards development, and technical training. Charlie was also a member of NECA’s Academy of Electrical Contracting. Charlie’s experienced team of industry experts keep the CQD dialogue and discussions active and informative in the spirit of the man himself, as he wanted.
NECA STANDARDS: NECA publishes the National Electrical Installation Standards™ (NEIS™), a series of ANSI-approved performance and quality standards for electrical construction. Visit NECA-NEIS.org for more information. NEISÃ” can be purchased in three formats: as paper books, on CD, or as electronic downloads.
NECA SAFETY PRODUCTS: NECA publishes valuable electrical safety books and CDs for the industry. Visit necanet.org/store to view or purchase NECA safety products.
CONTACT US: To submit a Code question, subscribe, or unsubscribe from this list, please e-mail: firstname.lastname@example.org.
© 1999 – 2014 National Electrical Installation Standards. All rights reserved.
Brought to you by NECA. NECA is the voice of the electrical contracting industry NATIONAL ELECTRICAL INSTALLATION STANDARDS, NEIS and the NEIS logo are registered trademarks of the National Electrical Contractors Association.
Created by Matrix Group International, Inc.