Standards as High as Your Own
NECA Online Help Desk Please leave a message
Re: CQD answer published Thursday, March 29, 2018 -Cooking appliance Tap Conductors
1) Good morning, If I understand 210.19(A)(3) Exc. No. 1 correctly, your answer did not specify the conductors referenced in the exception are those supplied with the appliance and not field-installed branch circuit conductors such as 12/2 NM-B cable. I believe the last sentence of the exception indicates this intent. Maybe this is a place where we could clarify the language a bit? Yeah, I know, you look forward to my Public Input! Thanks for your service. J Grant Hammett
2) I agree with the answer given for the tap conductors supplying the microwave from the range branch circuit. In addition, the tap conductors would have to be hard-wired to the microwave, otherwise 210.21(B)(3) would apply if installing a receptacle outlet. The receptacle would need to be rated for the branch circuit overcurrent protection per Table 210.21(B)(3). Tom Sieracki
Hey J Grant and Tom thanks for your comments.
1) The last sentence of 210.19(A)(3) Exception 1 limits the tap length to that needed for servicing the appliance such as if it needs to be removed from a cabinet while still being connected to the wiring method. The second to the last sentence includes appliance leads as part of the tap but does not prohibit field installed tap conductors.
2) Tom, you are correct receptacles would need to be protected as stated in 210.21(B) so a 15 or 20 ampere receptacle would not be allowed.
ABOUT CQD: NECA’s Code Question of the Day (CQD) is a leading National Electrical Code® forum for NECA and the industry. The CQD generates a lively dialogue and relative practical and Code-based responses to an ever-increasing and interactive audience.
IMPORTANT NOTICE: All answers are based on the latest edition of the National Electrical Code®, unless the question requests a response based on a specific edition. This correspondence is not a formal interpretation of the NEC®. Any responses expressed to the questions are opinions and do not necessarily represent the official position of NECA, NFPA, or any technical committee. In addition, this correspondence is neither intended, nor should it be relied upon, to provide professional consultation or services.
ABOUT CHARLIE: Charles M. Trout, better known as Charlie, was a nationally known NEC® expert and author. He served on several NEC® technical committees and is past chairman of CMP-12. In 2006 Charlie was awarded the prestigious Coggeshall Award for outstanding contributions to the electrical contracting industry, codes and standards development, and technical training. Charlie was also a member of NECA’s Academy of Electrical Contracting. Charlie’s experienced team of industry experts keep the CQD dialogue and discussions active and informative in the spirit of the man himself, as he wanted.
NECA STANDARDS: NECA publishes the National Electrical Installation Standards™ (NEIS™), a series of ANSI-approved performance and quality standards for electrical construction. Visit NECA-NEIS.org for more information. NEISÃ” can be purchased in three formats: as paper books, on CD, or as electronic downloads.
NECA SAFETY PRODUCTS: NECA publishes valuable electrical safety books and CDs for the industry. Visit necanet.org/store to view or purchase NECA safety products.
CONTACT US: To submit a Code question, subscribe, or unsubscribe from this list, please e-mail: firstname.lastname@example.org.
© 1999 – 2014 National Electrical Installation Standards. All rights reserved.
Brought to you by NECA. NECA is the voice of the electrical contracting industry NATIONAL ELECTRICAL INSTALLATION STANDARDS, NEIS and the NEIS logo are registered trademarks of the National Electrical Contractors Association.
Created by Matrix Group International, Inc.